James was here on time, performed the inspection and tests. He wore a mask and booties to cover his shoes. A definite compliment to your company. Very nice person and very thorough. Definitely would recommend.
01/18 Sch w Ghada via email 10A-3P Portable Extinguishers Inspection ***NEW CUSTOMER 1/2017*** Annual Inspection Extinguisher Equip Desc: Inspect (2) Exts Deficiency: Number of Extinguishers Left at Job: 2 condemned 5lb ABC extiguishers Renovations in progress in locations where 2 extinguishers were. They will be replacing extinguishers when work is done. Deficiency for 5 lb ABC Left side entrance to prayer room: 5lb abc extinguisher due for 6 year maintenance
Annual Emergency/Exit Light Inspection Equip Desc: (15) Emergency Light(s) Annual Extinguisher Inspection Equip Desc: (2) Extinguisher(s)
Portable Extinguishers Repair
Sch. & meet w/ Carlos 530-600 am Kitchen Suppression Inspection ***NEW CONTRACT BEGAN 01/2019*** Semi-Annual Kitchen Inspection Equip Desc: (1) ANSUL PIRANHA 13+13 Inoperable Deficiency for Ansul Piranha 13+13 Kitchen next to mgr office: Detection line failed to activate due to excessive grease buildup under hood 7 corner pulleys 12 Ansul detectors 5 sticks of conduit 50ft steel cable 5-6 hour labor