All employees I have ever dealt with have been extremely knowledgeable, courteous and professional. They take the time to answer all questions and complete the job !
ali /10am-11 /see ali Ali's phone number is 410-812-4398. Please make sure he will be there for both inspections so we can explain what needs to be done to fix it, if anything. Kitchen Suppression and Portable Extinguishers Inspection ***NEW LOCATION BEGAN 10/2020*** Semi-Annual Kitchen Inspection Equip Desc: (1) Ansul 6 Gallon System ***NEW LOCATION BEGAN 10/2020*** Annual Extinguisher Inspection Equip Desc: (5) Extinguishers Inoperable Deficiency: Ansul 6 gallon: Detection line failed to activate due to excessive grease buildup **Fryer, flat top griddle lacks detection** Parts needed to complete repair: *8 Ansul detectors 20ft conduit 30ft cable 2.5-3 hours labor Expired 101-30 cartridge MFD 2008 **Missing bolt for slack bar** Inoperable Deficiency: Ansul 6 gallon: Clogged duct & plenum nozzles 1 (1n) 2 (2w) Clogged salamander nozzles 2 (1n) Deficiency: Missing extinguisher (Rear kitchen exit) 5lb abc extinguisher due for 6 year maintenance (Rear patio door)
Portable Extinguishers Inspection
Annual sprinkler inspection