Response from Guardian Fire Protection Services, LLC:
Jeffrey, thank you very much for your feedback.
I called Guardian Fire by chance, we were looking for another fire safety provider and I called them, left a message and they called me back immediately. They came through for us with great services & good prices on our alarm, sprinkler inspections and a good deals on the repairs
Kitchen Suppression and Portable Extinguishers Inspection
hakeem 7-730 Kitchen Suppression Inspection Semiannual Inspection Dept: KITCHEN Equip Desc: (1) ANSUL 3 GAL Alarm Int: Yes
Portable Extinguishers and Emergency / Exit Lights Inspection
MR SONG 8 MR SONG is meeting you 1-443-851-8215 Kitchen Suppression Inspection ***NEW CUSTOMER 01/2019*** Semi-Annual Kitchen Inspection Equip Desc: (1) Ansul 9 Gallon System Inoperable Deficiency for Ansul R102 9G Kitchen: Ansul 9 gallon: Some deficiency’s remain from last inspection **Ansul automan will need to be replaced due to corrosion. (WATER DAMAGE)** **Manual or electrical gas reset relay needs to be installed.** **Local bell not operating properly (low humming sound)** **ELECTRICAL SHOCK HAZARD on ALTO shaam. **REGULATOR TEST DUE MFD 2008 (2) regulator hoses are needed due to 12 yr maintenance** **Remote pull block visually by fridge.** Needs to be relocated or fridge removed! Detection line failed to activate due to excessive grease buildup in hood. PARTS NEEDED TO COMPLETE REPAIR: 10- Ansul detectors 3- corner pulleys 20ft conduit 30ft cable 3-4 hours labor **Night time repair suggestions