Brian was a pleasure to work with. Very efficient service.
410 257 5225 spoke to carrey 12-2 Portable Extinguishers Inspection Annual Inspection Dept: EXTING Equip Desc: (19) EXTINGUISHERS Deficiency: Number of Extinguishers Left at Job: 7 1)10lb due for hydro test 5) due for 6 year maintenance
ed 1130-1230 must wear mask MEETING YOU DO NOT DROP Kitchen Suppression Inspection Semiannual Inspection Dept: KITCHEN Equip Desc: (1) RANGEGUARD 2.5 GAL Alarm Int: Yes Deficiency for RangeGuard Unknown 2.5 Gallon Right side of hood: Range guard 2.5 gallon **UL 300 upgrade needed** **Range Guard tank due for hydro test (MFD 2007) **Pull station is used as terminal detector. **Pull station exceeds height requirements of 48 inches
Portable Extinguishers Inspection