Dwayne explained the process; completed what he could. Once our gas line is reconnected, he can finish his install and inspect.
Never had any issues with Guardian in the 5+ years they been serving this property.
on time as promised
Service Tech Thanh Nguyen complete an annual fire alarm inspection at our commercial office building. He was thorough, professional and very efficient. He represents Guardian well with his work ethic. Much appreciated.
9/10 Scheduled with Terry 301-431-2800. Please call when on your way so she can put the system in test. 10-2 Kitchen Suppression Inspection Semiannual Inspection Dept: KITCHEN Equip Desc: (1) ANSUL 3 GAL & (1) ANSUL 6 GAL Alarm Int: Yes Inoperable Deficiency for Ansul R-102 6-gallon Main kitchen (left side of hood): 6 gallon Ansul system, when system is activated the FACP gets a signal, But there is no bell/alarm or strobe that is activated in response to that signal.
9/13 Scheduled with Charles 301-767-5812. Call prior to arrival as he will meet you on site. 11-1 Kitchen Suppression Inspection Semi-Annual Kitchen Inspection Equip Desc: (1) Ansul 3 Gallon System
9/10 scheduled with Ngussu 301-332-4355. arrive between 7/730am Portable Extinguishers and Kitchen Suppression Inspection Annual Inspection Extinguisher Equip Desc: Inspect (3) Extings (1) ANSUL R-102 3-gallon System Test Passed 1/16/14 1" Mechanical Gas Valve BELL 240-839-7918 7AM ONLY