He was knowledgeable and swift. Thank you!
Brandon was very helpful today with finding the source of my problems.
Our fire extinguisher technician was wonderful. He was very thorough, and made sure he didn't leave until every one of our extinguishers was located. I was very impressed.
The gentlemen who came to do my sprinkler inspection were thorough, professional, and seemed to have my best interest in mind. They shared their concerns with me in a way that was easy to understand and addressed all of my concerns.
James has been for nearly all of my services on the fire system. He is very knowledgeable in his trade and my facility. Please continue to send him and if he isn’t available cancel and reschedule.
Technicians were both great. Arrived on time and got the job done quickly.and efficiently!
brandon 1030a Kitchen Suppression Inspection ***NEW CUSTOMER 4/10/2020*** Semi-Annual Inspection Kitchen Equip Desc: Inspect (1) Kidde 4 Gal. Inoperable Deficiency for Ansul R-102 3G Rear prep area: Electrical shock hazard still remains (Vulcan) oven didn’t shout off when system was tested. **Electrical shock hazard** **Also the exhaust isn’t interlocked to the fire suppression system neither.**
Kitchen Suppression Inspection