This gentleman came in and completed the task in a timely manner and even was able to explain exactly what it was he was doing and why. Most companies send unfriendly contractors to do the work and this was by far one of the most enjoyable experiences. Very nice work completed by a very pleasant gentleman.
Great service, friendly customer service. Quick to respond to our needs, got us back up to date and current on our extinguishers.
Tech forgot to reset shunt trip breaker.
Technician arrived on time and was very professional. Our service was 100% complete.
Kitchen Suppression Inspection
LLOYD/8-830/SEE LLYOD 240 515 3312 MEETING YOU Kitchen Suppression Inspection Semi-Annual Kitchen Inspection Equip Desc: (1) PyroChem 300 System Inoperable Deficiency for Pyro Chem 300 3 Gallon Kitchen: Improper coverage above fryer and 4 burner range *plans and permits required**
tt confidence 12 Kitchen Suppression Inspection Semi-Annual Kitchen Inspection Equip Desc: (1) Ansul 3 Gallon System
9+6 gal ansul adam/9am Kitchen Suppression Inspection KITCHEN SYSTEM INSPECTION SEMI ANNUAL Deficiency: Ansul 9 gallon 2 out 3 cylinder are due for hydro testing (MFD 2006x2) Deficiency: Ansul 6 gallon 1 out of 2 cylinders are due for hydro testing (MFD 2006) Inoperable Deficiency: Ansul 9 gallon Detection line failed Parts needed: 7 detectors 30ft conduit 30ft cable 2-3 hours labor Inoperable Deficiency: Ansul 6 gallon Detection line failed (Pre UL-300) U shaped clips obsolete Parts needed: 4 Ansul detectors 15ft conduit 15ft cable 1-2 hours labor Deficiency: Ansul 6 gallon Pre UL-300 nozzles in duct and plenum 2 (1n nozzles need to be installed 2 (1w nozzles need to be installed Deficiency: Ansul 9 gallon Pre UL-300 duct and plenum nozzles 4 (1n nozzles need to be installed 4 (1w nozzles need to be installed Inoperable Deficiency: Chemical found in suppression lines, both Ansul 9 and Ansul 6 needs to be flushed and purged with nitrogen
pedro /10-1030/see pedro Kitchen Suppression Inspection Semiannual Inspection Dept: KITCHEN Equip Desc: (1) ANSUL 3 GAL & (4) EXT Alarm Int: Yes