Very courteous and polite
Wouldn’t want anyone else checking out my building , send us only Lee Foo 😉
Totally knocked it out of the park. Grand slam ! Touch Down with the 2 point conversion Completed Hat-Trick! No Boggies here, Hole in One! Lee Foo, was incredibly thorough! 👍 Thank you
Response from Guardian Fire Protection Services, LLC:
Arturo, thank you for such a great review of Lee and the services he provided. Your reivew is by far the most enthusiastic one we have received and I really appreciate it. Lee's a great guy and very pleased that he did so well for you. Thanks, Scott Agge, President
I have no experience , but Joe showed by example that he has all the experience
I have use them for many years and have never had an issue. Just wish they could come at time I need them and not when its convenience for them
Good to know Guardian employs such competent and courteous people to do their inspections. He was able to answer all my questions, and we have 30+ y.o. equipment in our kitchen.
Onsite for service/repairs. At arrival found 2 troubles on FACP. Replaced 4th floor Wheelock HSR by unit 405 to clear NAC 4 trouble. Replaced batteries at 2 boosters in suite 306 electrical closet to clear NAC 1 open. System normal at departure.
02/27 Jake 6am Kitchen Suppression Inspection Semiannual Inspection Dept: KITCHEN Equip Desc: (1) PYROCHEM 4.6 GAL Alarm Int: Yes
930am-10/ check in with Brian (571 296 5528/703 865 4333) alarms call anthony 571 459 0363 Kitchen Suppression Inspection Semi-Annual Kitchen Inspection Equip Desc: Ansul System Inoperable Deficiency: Ansul 3 gallon (Range hood) **No Gas Shut Off installed in ottoman** *SUGGESTIONS: Install gas shut off valve and interlock to 3 gallon fire suppression system
tt MANUEL 8am Kitchen Suppression and Portable Extinguishers Inspection Semiannual Kitchen Inspection Equip Desc: (1) Ansul R-102 9G Kitchen System(s) Annual Extinguisher Inspection Equip Desc: Extinguishers
Portable Extinguishers Inspection