Dwayne is a great technician and teacher for his co-workers. I never have to worry about a job that he has done.
I consistently get great service from the Guardian staff.
he did a great job as always.
Guys always do a great and professional job.
Kitchen Suppression Repair
mr gusippi 9am FLUSH SYSTEM PER ANSUL MANUEL Portable Extinguishers and Kitchen Suppression Inspection Annual Inspection Dept: EXTING Equip Desc: (8) EXTINGUISHERS Ansul R-102 6 Gallon Kitchen: Semiannual Inspection Dept: KITCHEN Equip Desc: (1) ANSUL 6 GAL Alarm Int: Yes
paul 7a Kitchen Suppression Inspection Semiannual Inspection Dept: KITCHEN Equip Desc: (2) ANSUL 6 GAL, (1) ANSUL 3 GAL, (1) ANSUL 12 GAL Alarm Int: Yes
brain 8-1 Kitchen Suppression Inspection Semi-Annual Kitchen Inspection Equip. Desc.: (2) ANSUL systems: (1) 6-gallon & (1) 1.5-gallon Inoperable Deficiency for Ansul R-102 6-gallon: Ansul 6 gallon and 1.5 gallon systems: **Electrical shock hazard on smoker and SouthBend oven**
lynn / 930-1230 Kitchen Suppression Inspection Semiannual Inspection Dept: KITCHEN Equip Desc: (1) ANSUL 1.5 GAL Alarm Int: Yes Inoperable Deficiency for Ansul R-102 1.5 Gallon: Same deficiency’s remain from last inspections: **System lacks protection and detection Parts needed: add 1 detector above 6 burner range replace 2 pre-ul 300 nozzles over range with (1) 245 & (1) 1F add 1N nozzle over griddle