This is the 4th year we have had our site checked by Guardian Fire Protection Services. I'm always impressed by how friendly and professional their technicians are. Thanks to Tim M. who was very helpful, on site early, and incredibly professional.
Emergency / Exit Lights and Portable Extinguishers Inspection
12/30 RIGO not 24 hrs 4-5A KGUARD HYDRO Portable Extinguishers and Kitchen Suppression Inspection Annual Inspection Extinguisher Equip Desc: Inspect (4) Exts Semiannual Inspection Dept: KITCHEN Equip Desc: (1) ANSUL 6 GAL/(1) ANSUL 3 GAL/(4) EXT Alarm Int: Yes Inoperable Deficiency for Ansul R-102 3 Gallon Grill: Kitchen Hood: grill Need to rerun a new detection line. Terminal detector not secured, could lead to a discharge. 3rd detector shifting up to ceiling of hood. (3) Ansul detectors (6) feet of conduit (12) feet of cable (3.5) hours of labor
Portable Extinguishers and Emergency / Exit Lights Inspection