Chuck is knowledgeable enough to recommend exactly what I needed. If I ever need more fire protection I’ll call Chuck.
service was timely
Always professional, does a great job.
Brenda was so informative of the maintenance that she was completing. If the fire extinguisher was out of date she showed me where I needed to look for the date. We had a few extinguishers that needed to be removed due to DOT and she provided the documentation needed to.
Planning to use again next year
service techs are professional and well mannered. They show up on time, do a great job, and clean up there mess.
You have been providing great service for many years. We thank you here at the Backstreet
Fire Suppression Inspection KITCHEN SYSTEM - ZONE 4 - BFR-10 - HYDRO 2013
Gas Station Suppression, Portable Extinguishers, and Emergency / Exit Lights Inspection GAS STATION - QTY UNKNOWN GS DO FX AT SAME TIME FIRE EXTINGUISHERS - QTY UNKNOWN FX TO BE DONE WITH KS EMERGENCY LIGHT SPOT CHECK - REPAIR AS NEEDED EL TO BE DONE WITH GS Work with electrician to replace Sentinel control head
Kitchen Hood Suppression System - NON COMPLIANT Recently one of our licensed technicians was at your location to perform the service on your fire suppression system. During that inspection the following deficiencies were found on order 13849767 Plenum and duct nozzle need to be re-positioned as they are installed back to back and this is no longer listed as proper protection. Replacement nozzles required due to heavy grease build up. Auto detection system requires replacement due to the amount of grease in the auto detection conduit and fittings CLIENT RESPONSIBILITY - Exhaust system should have grease cleaning due to current condition. Repair of these deficiencies is essential to overall life safety. Please see attached compliance quote. If you have any questions, feel free to call me. Thank you Mike McDonald 603-988-5512 Fire Suppression Repair Extremely heavy grease build up. Plenum and duct nozzles need to be repiped and replaced conduit and detection line should be replaced Bot
Portable Extinguishers Service Call
Fire Suppression Inspection Kitchen Systems - Zone 4 RG 6.0 G, old style Hydro: 2004 KS TO BE DONE WITH FX