Tri-State Fire has been extremely accommodating to our facilities needs! Great customer service from the ladies in the office to the men in service! Highly recommend!
Did the inspection in a timely fachion
Chris was awesome! He was personable, informative & very knowledgeable! Tri-State is lucky to have him as an employee!
Matt was in and out quickly without disrupting any of our business for the day. He was even patient with US since we had another issue going on when he came to visit!
Tech did a great job, THE PROBLEM IS COMPUTER PROGRAM TO TRY AND PRINT REPORT, COULD NOT GET IT PRINT A READABLE COPY!! wasted 6 sheets of paper, BUT YOU GOT TO SAVE PAPER !! I THE COST OF INSPECTIONS HAS GONE UP WOULD NOT RECOMEND YOUR COMPANY TO ANYONE
Portable Extinguishers, Gas Station Suppression, and Emergency / Exit Lights Inspection FIRE EXTINGUISHERS - QTY 9 FX TO BE DONE WITH KS GAS STATION - QTY 1 ATD-80 x20 GS DO FX AT SAME TIME EMERGENCY LIGHT SPOT CHECK - QTY 14 REPAIR AS NEEDED EL TO BE DONE WITH GS
Gas Station Suppression and Emergency / Exit Lights Inspection GAS STATION - QTY UNKNOWN GS DO FX AT SAME TIME EMERGENCY LIGHT SPOT CHECK - REPAIR AS NEEDED EL TO BE DONE WITH GS Inoperable Deficiency: Emergency light: 2@ 2x4 fluorescent emergency lights in back room (the only 2 elights) did not respond to button test. Women's room fluorescent emergency light over sink failed to respond to button test. Electrician needed to repair. Confirmed 4/3/18 NL Inoperable Deficiency: Previous emergency light issues still exists. 2x 2x4 over head fluorescent e-lights failed button test. 1x emergency light above sink in women's room also failed button test. Electrician needed for repairs.