Fire Suppression Inspection Pre-Inspection on Kitchen Suppression Inspection Deficiency: Ansul system: Fire alarm and electrical shut down need to be tied in. Also Ventilator controls also need to be tied in. Dampers are not opening properly when exhaust fans are turned on.
Portable Extinguishers Inspection FIRE EXTINGUISHERS - QTY 2
Portable Extinguishers Service Call FIRE EXTINGUISHERS - QTY 3
Portable Extinguishers Inspection FIRE EXTINGUISHERS - QTY 65
Portable Extinguishers Repair FX located 1st floor south stairwell is in the red. looks like it was serviced in 2016
Portable Extinguishers Inspection