The repair items Jeff found helped us negotiate the costs and saved us a whole bunch of money.
Leak found at master bathroom sink drain.
Rail spacing does not meet current standards and we recommend repairs by a qualified licensed decking contractor.
As part of regular and on going maintenance in a home bathroom and laundry room vent fans should be cleaned. This is something a home owner can do themselves but is often overlooked. We recommend cleaning them every six months and don’t forget to check the HVAC filters as well.
Cracked skylight could lead to leaks in a home. Skylights should be checked often for cracks and leaks as part of regular and ongoing maintenance. This skylight cover may have to be replaced. Have The Property Inspection Pros come inspect your roof and skylights. We are your honest San Diego Real Estate inspection company that you can trust.
Single family home inspection found a number of trip hazards in the front walkway and an entire circuit of outlets that did not work. The water heater is failing and has a number of safety deficiencies that should be corrected. A number of screens were found to be worn or missing and stairs at the rear of the property is missing a railing. This is a safety concern and should be corrected. The moisture testing reveal elevated levels in the master bath and we recommend further evaluation. The floor around the toilet is spongy and there could be an active leak.
Two cracked skylights and a worn asphalt roof on this town home. Active moisture stains in the HVAC closet result from a disconnected drain line. We recommend installing a drain pain to prevent future and repairs by a licensed contractor.
Missing fireplace damper clamp and waste pipe plumbing leaks were discovered in addition to leaking faucet handles. Licensed contractors are always recommended for repairs or replacement.
3 story condominium inspection revealed an aged air conditioning unit, kitchen sink leak and elevated moisture near the master bathroom shower. We recommend repairs or replacement by a licensed HVAC contractor or plumber.
Water pressure was found to be high during the water pressure test. Water pressure above 80 PSI is considered to be high. We will recommend the water pressure to be adjusted within acceptable limits by a licensed plumber. If it cannot the pressure regulator may need to be replaced.
Smoke detectors are recommended to be replaced every 10 years for safety. This beautiful San Marcos home has newer smoke detectors and are installed in the appropriate locations throughout this home and bedrooms. All of our home inspectors are certified pros which makes a difference when choosing the best property inspector for your needs.
Thermal scan of the kitchen appliances. All we’re older but in good working condition. We will recommend getting a home warranty which covers them.
Inspection report will recommend reducing high water pressure, leak pan for the hot water heater that will drain to the exterior.
San Marcos Home Inspection. Thermal scan revealed a leak at the water heater supply pipe. At The Property Inspection Pros we are all certified home inspectors, professionally trained and use the best equipment and technology available.
AC unit did not operate when tested. Agents can build an easy request for repairs right from our reports.
Conducted a pool and spa inspection at the time of the home inspection.