In the process of selling, techs found a couple problems and I was able to get them fixed prior to sale.
Semi annual checkup. No issues.
ac check trane
trane heat pump diagnostic
Fall service on a Goodman heat pump!
Performed spring service on Rheem system.
Performed spring service on train systems
Complete a two system maintenance and found the UV light not working on the second floor. I have a price quote of $189.00 to repair UV light.
Found the compressor pulling lock rotor amps, replaced the dual cap and the compressor saver kit.
Complete ac maintenance of a Amana heat pump system. Recommend air cleaner, and surge protector.
Performing a cool check on a Goodman. Unit
Performed annual heating maintenance on a Rheem heat pump and air handler. Found no problems to report. HVAC system operating properly at this time.
Clayton A/C maintenance