Response from 72 Degrees Heating and Air Conditioning:
Thank you Jennifer! We greatly appreciate your review
New furnace cabinet installed!
Diagnostic on a Amana heat pump. Line set is frozen from air handler to condenser...
Found breaker for air handler tripped. Turned breaker off all the way and removed heat strips to verify they were not grounded out or broken. Checked wiring inside disconnect box and found nothing loose or burnt. Breaker was warm to touch. Breaker may be going bad and may need to be replaced
Blower fan board.
I am performing a semi annual maintenance on a 1 year old system.
Here for demand service on a Goodman heat pump split system