Don was very friendly and done a great job!!
Tim came and helped me when our air had stopped working. It was easy to set up the appointment- the company was very accommodating. Tim called me when he was close. He listened to my concerns and began working. He explained what the problem was and step by step how to fix it. When my husband called he stopped and explained everything again. He was respectful and answered the MANY questions I had! I will recommend Tim and this company to everyone I know! His card is in my wallet and on the fridge!
Tim came out and did a complete service and explained everything he was doing. He cleaned our unit and check all voltages, levels and other readings relating to our unit. He was very friendly, informative and we will ask to have him come for our services in the future. Highly recommend Tim and 72 degrees for anyone needing air / heat work.
Spring service on a Goodman Package unit.
Summer maintenance on 2 Amana Units!
Diagnostic on a Goodman Package unit. Exploded Start Cap and Hard start kit.
Diag on a Westinghouse heat pump .... Blown compressor
Need to come back and repair copper line to TXV that we replaced incorrectly in 2016, no charge for diagnostic due to error by us per John.
Winter tune up!
Technician performed a 34 point inspection and tune up of the heating and cooling system. System is operating properly at this time.
Performed maintenance on gas package HVAC system. Checked gas pressures, safeties, capacitors, burners and overall operation. Installed new thermostat at customer's request.
Cleaned and serviced Miller heat pump
Cleaned and serviced Westinghouse heat pump
I am performing a Warranty Demand Service on an Amana system.
demand service on 19 year old Goodman heat pump
Checking a no cooling problem on a Goodman heat pump
Checking a no cool problem on a Westinghouse heat pump.