Very prompt, knowledgeable and personable installers!
A+ lived up to its name. BG was very knowledgeable and professional. He was thorough and did an outstanding job!
My neighbor was right...A+ is great to work with
Lennox 3Ton 20Seer Heat Pump Split System.
Performed leak search and found reversing valve leaking after noticing the unit was extremely low on refrigerant
After troubleshooting unit I found the unit a little over charged. Corrected the mistake and units are running as they should be .job completed
H/o needs another light in crawl space unit I only had one on the truck and added 3 lbs of refrigerant
Replaced indoor blower motor unit is running at factory specs no other problems or concerns. Job completed
When I arrived h/o as well as daughter is concerned about a high pitched whistle along which a sound on startup and after inspection I found indoor blower motor does make a sound on startup but couldnâ€™t get the winding/ whistling sound but knowing that thereâ€™s only mechanical part that deals with airflow that could possibly make that noise. My diagnosis is the blower should be replaced. Informed homeowner of findings and diagnosis. No other problems or concerns.
Unit is low on refrigerant , performed a courtesy leak search and found a leak in the reversing valve , informed h/o and advised for it to be replaced. Estimate was emailed and price as well job completed
After troubleshooting I found unit low on refrigerant. The reason their bill is high is because outdoor isnt coming on due to low refrigerant and indoor is blowing emergency heat all the time. Problem found .
2019 Ruud system maintenance 10/10/10 customer
Performed prepaid maintenance on a 2004 Goodman heat pump split system. On the indoor unit found the evaporator coil in really bad shape due to heavy corrosion also the capacitor on the blower motor is causing it to run higher amps. The outdoor unit has a rotting accumulator and the compressor is over amping .Customer is asked to speak to a comfort adviser about possible replacement office is calling to set up the appointment.
2018 Ruud No heat. Checked system and determined blower motor to be bad and in need of replacement. Gave estimate and got approval for repair. Replaced motor and started system. Checked pressures. Checked motor and compressor amps. Unit is working properly at this time.
2015 Goodman system braise repair leak on true suction at condenser charge system 7 pounds 410A
Replaced warranty evaporator coil.
2015 system is determined to have a leaking evaporator coil in need of warranty replacement.
2004 Goodman Fujitsu mini split Checked pressures. Checked voltage and connections throughout. Checked amp draw on compressor and fan motors. Cleaned coils. Changed customer provided filters. Cleared drain lines. Units are working properly at this time. Replaced weak 30/5 capacitor on Goodman system. This is a R22 system. Evap coil is rusted. Unit has good pressures and is cooling properly. Customer signed up for Silver Cool Club