My neighbor was right...A+ is great to work with
2015 Goodman system braise repair leak on true suction at condenser charge system 7 pounds 410A
Replaced warranty evaporator coil.
2015 system is determined to have a leaking evaporator coil in need of warranty replacement.
2004 Goodman Fujitsu mini split Checked pressures. Checked voltage and connections throughout. Checked amp draw on compressor and fan motors. Cleaned coils. Changed customer provided filters. Cleared drain lines. Units are working properly at this time. Replaced weak 30/5 capacitor on Goodman system. This is a R22 system. Evap coil is rusted. Unit has good pressures and is cooling properly. Customer signed up for Silver Cool Club
2018 system is currently in good working order. Adjusted air pressure and reset bypass.
2019 Ruud system maintenance
Replaced reversal valve solenoid and unit responded very well, no further issues are suspected or presently detected.
Customer is experiencing a slow shift of the reversal valve causing unwanted noise. The noise is indeed abnormal, and indicates a problem with the reversal valve. The reversal valve coil should be replaced as a first course of action. Solenoid Coils often become weak, causing this issue.
2019 Ruud Checked pressures. Checked voltage and connections throughout system. Checked amp draw. Checked capacitor. Cleaned coils. Checked airflow. Cleared drain line. Unit working properly at this time. Informed customer of growth inside air handler
Replaced blown capacitor, cooled overheated compressor, and restarted system with no further issues detected at this time.
Warranty call. Found outdoor unit not running. Board was flashing a code of temperature sensor lockout. Cut power to board and restarted system. Checked air handler in attic also. System is operating but I changed the sensor wire on the heat pump in case it has an intermittent fault. Cycled system and educated clients on heat pump system and thermostat operations.
Checked/changed filters, checked thermostats, checked heating elements and blower amps, checked evap coil, checked drain pan and line, checked capacitor, checked fan and compressor amps, checked pressures, cleaned condenser coils. Installed UV light. 1 system: 2018