On time, knowledgeable, fast
Response from A+ Heating & Cooling- Electrical:
Hi Ruth, glad to hear Kevin took excellent care of your Air Conditioning unit.
Performed routine maintenance on goodman unit 2015
2010 evaporator coil is indeed leaking, it is not however advised to perform this repair. System is out of warranty as of last week and nearing the end of its life expectancy. System replacement recommended in lieu of repair.
Older Rudd gas pack replace pro 5000 thermostat
Performed routine maintenance on a 2014 goodman
Service call on a 2013 Goodman split heat pump. Upstairs system. The heat pump wasnâ€™t starting due to a bad capacitor. Mail hard copy she doesnâ€™t do email
Please see repair estimate.
2004. Found L1 pin blown from compressor. Compressor would need to be replaced in order to restore operation, this repair is however not advised. System is in need of replacement.
Service call. I checked all 3 systems and could not find any problems. 3-2016 Goodman split heat pumps.
Prepaid maintenance on a 2010 American standard heat pump split system
Performed maintenance tuneup on 2017 Ruud unit. Checked all connections and readings. System is operating properly at this time. Found mold in air handler. Ordering uv light and added pan strip.
Silver service on 2 heat pump systems
Performed the seasonal maintenance per agreement on a 2014 Bryant split heat pump.
Install maintenance 1 of 2 1 system: 2019