On time, knowledgeable, fast
Response from A+ Heating & Cooling- Electrical:
Hi Ruth, glad to hear Kevin took excellent care of your Air Conditioning unit.
Re-cleared and addressed drain line. The P-trap piping seemed to be too deep in the condensate pump.
Checked drain assembly. Put cap back on condensate pump. This had created a double vent. Unit is working at this time
Warranty call. No power at tstat. Found water in SS2. Cleared p-trap and checked condensate pump. Unit is working at this time
Found a 2008 Goodman unit to be low on r22 and the system freezing up. Comfort advisor is scheduled to come out tomorrow and speak to homeowner about both systems due to the other systems age. No info on the unit and homeowner said it is the original with the home 1995
replacement evaporator coil 1 year part, 1 year labor on coil
Remade connections in disconnects.
2x2011 Heat pump maintenance
2013 system was found to have a completely restricted air filter. Additionally the system was slightly overcharged with refrigerant. The dual run capacitor in the condenser was also depleted and out of tolerance. No further issues were presently detected with the equipment.
Performed routine maintenance on a Goodman unit
2017 and 2019 ruud heat pump systems. Checked voltage, capacitors, amp draw, connections, contactors, pressures and cleaned coils. Put new batteries in thermostats, waxed off units, and insure all connections were proper, and tightened down any loose connections throughout systems. Both units are working properly at this time no issues were found.
Replaced breakers. Helped sit equipment in place
Demand call on a 2009 train heat pump split system. Found the unit low on gas ,this is r22.The filter dryer on the outdoor unit is leaking needs to be replaced. Customer has asked to speak to a comfort adviser about replacement. Jack is scheduled for 3 PM today.
Service call on a 2017 Bryant split heat pump. The 5 amp fuse was blown in the air handler. I traced the low voltage wiring and found the yellow wire in the heat pump shorted to the cabinet. I repaired the wire and replaced the 5 amp fuse.