Install maintenance 1 of 2 1 system: 2019
Clean and check
One man one hour
To replace the filter dryer. Non warranty, braze in.
Install maintenance 1 of 1. 1 system: 2018
Installed a new Condenser fan motor for the police station back end unit. Started system. Compressor is struggling to turn over. Installed a start booster for the compressor. Restarted system. Compressor and motor have good run and start amps now. Finished checking over rest of system. Ok to send invoice to BSL per office. Invoice for fan motor has. Already been sent.
Diagnostic call. Found power going to unit, contactor pulled in , power across contactor but condenser fan motor and compressor were not running. Cooled down compressor and start winding closed. Restarted system. Condenser fan motor is going bad. It had stopped running and made the compressor go off on internal overload, office is ordering a new 1/6 hp 815 rpm, .9 amp condenser fan motor. Condenser fan motor
Service call. Police department front office.
Replaced GFI outlet
Return with parts