On time, knowledgeable, fast
Response from A+ Heating & Cooling- Electrical:
Hi Ruth, glad to hear Kevin took excellent care of your Air Conditioning unit.
Checked and inspected propane gas pac. Unit came on when called and turned off when temp was reached . Checked duct work under house, ductwork is old but still intact, checked heat exchanger, inducer, and flame everything seems to be running rite. Advised him to call gas company to see if anything changed since he moved in a year ago. Job completed
Warranty motor replace 2018 ruud package unit
Performed routine maintenance on a Goodman system and found the drain to be heavily clogged as well as water marks from the secondary pan. Freed up drains but pan will need replacement. Also found the evaporator coil to be heavily rusted and is a potential concern. Unclogged drains and cleared water out of the secondary.
Rewire fan and switch
Replaced breaker for heat and AC replaced whip on Ac
2 Bryant heat pump systems. Checked voltage, amp draw, connections, pressures, capacitors, contactors, tested float switches, cleaned coils, drain lines, and ensured all connections throughout were properly tightened down and in proper place. These systems are working properly at this time no issues were found.
See return for service
New install was not running due to original condensate pump is bad it will have to be replaced
Changed two breakers Replaced whip on AC
Supervised job. Need to return to do final inspection
Re-cleared and addressed drain line. The P-trap piping seemed to be too deep in the condensate pump.
Checked drain assembly. Put cap back on condensate pump. This had created a double vent. Unit is working at this time
Warranty call. No power at tstat. Found water in SS2. Cleared p-trap and checked condensate pump. Unit is working at this time
Found a 2008 Goodman unit to be low on r22 and the system freezing up. Comfort advisor is scheduled to come out tomorrow and speak to homeowner about both systems due to the other systems age. No info on the unit and homeowner said it is the original with the home 1995
replacement evaporator coil 1 year part, 1 year labor on coil