Great service from a polite technician
Joshua was superb..... very thorough, knowledgeable & professional. He is definitely a valuable asset to A+ as well as to us, all the clientele.
I would like Kevin to come when it’s time to service my ac
On my install
great all but the price
When you install a brand new HVAC system, you don’t expect to have to call for service 7 days later, but that was the case. BG had nothing to do with the installation, but he identified and corrected 3 significant issues with the system that prevented it from heating our home. He explained what he checked, told me what he had to adjust or fix and last night (while not as cold) the system kept the house at the expected temperatures. Thank you BG!
kevin did a very good job and rates a 10 if that is the highest number and he was also very nice
Very knowledgeable and very neat
A+ is well represented by Joe Walters. Once again he worked hard to get our system back heating our home. I know we have more decisions to make, but I am glad we have A+ and experienced people like Joe working with us.
Service was part of contract no additional charge
Chris was very knowledgeable and quick to solve the problem
2012 Goodman 2012 Goodman 2016 Goodman Checked pressures. Checked voltage and connections throughout. Checked a,p draw on compressors and fan motors. Checked capacitors. Checked safety switches. Cleared drains. 2012 Goodman on the right side of home is low on refrigerant. Due to the age of the system, efficiency and no warranty replacement is recommended. Customer is getting a quote from Robert.
Performed routine maintenance. Cleaned indoor coil and found indoor cabinet rusting away on the bottom due to a leak (cabinet is pitched) from installation (not us) and bottom is corroding. Homeowner will look into new unit in future. Outdoor was low on refrigerant so 2lbs was added at customers expense. Job completed
Performed routine maintenance on a trane system 2021
Performed maintenance. Educated homeowner on how heat strips operate. And answered all questions he had. After completing my Maintenance homeowner was interested in a pan strip, installed a pan strip . Job completed
Add light and switch in pantry,Hang new ceiling fan.
2011 Ruud package HP system maintenance System was locked out on low pressure due to a limb wrapped around the condenser fan blade removed limbs and cleaned up unit. system is working at this time but is showing advanced wear and deteriorating due to age.
2012 Ruud 2020 Lennox systems maintenance
Preformed a maintenance on a Ruud unit. Indoor unit: I checked amps on the blower motor, I checked the capacitor, I checked the float switch, I checked the coils, I checked the drain pan and drain line, I checked the electrical wires and connections, I checked the heating element. Outdoor unit: I checked amps on the compressor and fan motor, I checked around the contactors and the board, I checked the capacitor, I looked into the unit for rubbed wires and rust, I vacuumed the drain line and I vacuumed the bottom of the unit, I checked behind the disconnect, I washed the unit down with water, the only thing I noticed was that the disconnect and the unit had a light amount of spider webs, for the indoor unit I noticed the coil, had a light/medium amount of rust.
Performed routine maintenance on a Goodman system 2015
Installation of a 16 SEER 1 stage Lennox Split System $9991.00
Capacitor Preformed a maintenance on a 2016 Trane unit. Indoor unit: I checked amps on the blower motor and induction motor, I checked the capacitor, I checked the electrical wires and connections, I checked the float switch, I checked the drain pans and drain line, I checked the flame quality. Outdoor unit: I checked amps on the compressor and fan motor, I checked the capacitor, the capacitor is a 35/5uf, I was reading 31.40/4.6, I replaced the capacitor, I checked around the contactors and the board, I looked into the unit for rubbed wires and rust, I vacuumed the drain line, I washed the unit down with water.
Preformed a maintenance on 2 Ruud heat pumps. Outdoor units: I checked amps on the compressors and fan motors, I checked the capacitors, I checked around the contactors and the boards, I looked into each unit for rubbed wires and rust, I cleaned out the bottom of the units, I vacuumed the drain lines, I washed the units down with water. Indoor units: I checked amps on the blower motors, I checked the float switches, I checked the electrical wires and connections, I checked the drain pans and drain lines, I checked the coils, I checked the supply and return lines, I cleaned the units down with cleaner.
Install s lock Too stiff in the cabinet up so when the blower motor came on the cabinet did not make a popping noise from the metal moving
Preformed a winter maintenance on a mini split system. I arrived at the job and started at the outdoor unit, I started by vacuuming the unit down, I the checked the electrical wires and connections, I checked the amps on the compressor, I cleaned the coils, I checked behind the disconnect, I then went to the indoor unit and checked the filters, I took them outside to clean them, I vacuumed out the filters and the indoor unit, I went back outside vacuumed the drain line and put the unit back together, I finished by washing the unit down with water.