Replaced 4â€ Flex run. 8â€ was replaced already?
Upon performing Maintenance and Repairs both thermal expansion valves were determined to indeed be defective and in need of replacement.
Returned per owners request in order to inspect ductwork. Ductwork was found to be ripped in multiple locations due to wildlife and attic.
Added a pound of refrigerant and advised client that system may not maintain 72Â° during peak summer days.
After performing a thorough inspection of both systems it was determined that both filter dryers are restricted (downstairs more so), as well as the condenser coils. Systems will run better than ever after performing these repairs. No further issues were presently detected.
Replaced whip and breaker.
Customer wants us to do Sheetrock and painting the we do not do
Whole home inspection