Two new disconnect boxes Two new whips Replaced breaker
Need to reschedule due to renters in the home. Contact owner, no answer.
2005 system was found without power to the thermostats, and subsequently the zone control panel. A transformer fuse was determined to be blown and was replaced. No further issues were detected with the system components at this time, system is currently in good working order. It should be noted that the equipment is come of age, and will require replacement in the foreseeable future.
Replaced 4â€ Flex run. 8â€ was replaced already?
Upon performing Maintenance and Repairs both thermal expansion valves were determined to indeed be defective and in need of replacement.
Returned per owners request in order to inspect ductwork. Ductwork was found to be ripped in multiple locations due to wildlife and attic.
Added a pound of refrigerant and advised client that system may not maintain 72Â° during peak summer days.
After performing a thorough inspection of both systems it was determined that both filter dryers are restricted (downstairs more so), as well as the condenser coils. Systems will run better than ever after performing these repairs. No further issues were presently detected.
Replaced whip and breaker.
Customer wants us to do Sheetrock and painting the we do not do
Whole home inspection