2018 Lennox gas pack package unit. Checked voltage, amp draw, connections, pressures, capacitors, contactor, put new wire nuts on thermostat wires, ensured all connections throughout were properly tightened down and in proper place, cleaned coils, drain lines, and cleaned off growth on unit, also cleared debris inside unit. This system is working properly at this time.
Perform tuneup on two 2003 train heat pump split systems. For the downstairs itâ€™s a package unit the compressor is running higher amps and it should also the filter dryer is showing signs of corrosion as well as the evaporator coil. On the upstairs unit the evaporator coil is in really bad shape . Both systems are running at this time though failure will happen in the near future due to these corrosion issues. Recommending replacement of both systems due to age and condition and overall efficiency. Homeowner is not ready to move forward since units are working.
Found tripped breaker in panel. Found two GFI receptacles that was tripped on the outside. Install receptacle for a timer for lights .