Perform maintenance on a 2016 Amana heat pump system. Checked all voltage amperage and capacitor all are good at this time. Checked float switch in pan switch both are running normal at this time. Blue ultraviolet light is operating normal at this time. Evaporator coil and condenser coil both look good. Replaced 20 x 20 x 5 MERV 11 air filter. Also checked customer concern of bubbling in ceiling checked ductwork to vents could not find any moisture at this time.
Performed routine maintenance on a 2019 amana Need to come back to replace 20x20x5 media filter
Add 6 inch run to master bedroom
2019 Goodman system Estimate for adding run to master bedroom
Return to replace 20x20 media filter. Pre paid
2019 Goodman Checked pressures. Checked voltage and connections throughout . Checked capacitor. Checked amp draw on compressor and fan motors. Cleaned coils. Cleared drain. Replaced pan strip. Merv 11 filter needs to be replaced, will have to order. Removed filter and customer is using return filters in the meantime. * see notes
Give quote for 22KW standby generator
Performed maintenance tuneup on unit. System is operating properly at this time. Installed pan strip.
Unit not cooling
Install WiFi tstat
Installed receptacle in garage for freezer.