2019 Goodman system Estimate for adding run to master bedroom
Return to replace 20x20 media filter. Pre paid
2019 Goodman Checked pressures. Checked voltage and connections throughout . Checked capacitor. Checked amp draw on compressor and fan motors. Cleaned coils. Cleared drain. Replaced pan strip. Merv 11 filter needs to be replaced, will have to order. Removed filter and customer is using return filters in the meantime. * see notes
Give quote for 22KW standby generator
Performed maintenance tuneup on unit. System is operating properly at this time. Installed pan strip.
Unit not cooling
Install WiFi tstat
Installed receptacle in garage for freezer.