Checked job. Wire and feeder are at proper burial depth now.
Extend ground to ground lug inside meter, sleeve uf wire for well pump in 1/2â€ carflex, pour concrete in feeder trench.
-Need to extend ground wire from first ground rod to inside top of line side of meter and terminate in small lug in meter compartment. Add another ground clamp at first rod and run your number 4 or number 6 copper to line side of meter compartment instead of replacing the whole run of copper to other ground rod. - Feeder conduit isnâ€™t 18â€ below grade. To keep from having to redo everything to get proper burial depth, get 2-3 bags of quikrete and dump over conduit so thereâ€™s 2â€ of quikrete over conduit. You wonâ€™t need 18â€ of ground cover if itâ€™s encased in atleast 2â€ of quikrete. - Bury UF cable for well pump 24â€ below grade before it emerges from trench at pedestal. Would be easier to sleeve in carflex and place beside feeder conduit before you pour quikrete in trench. If itâ€™s in carflex and encased in quikrete, then you wonâ€™t need 24â€ of ground cover.
Push wire an terminated meter an inside panel installed GFI at well
Build new service on new mobile home
Looked at job. Got Lisa to order proper wire for feeder. Also wired up customers outdoor AC while I was here. AC is attached to our permit.