Run circuit for subpanel to feed outdoor units. Run circuit for attic air handler, installed disconnects.
2019 Lenox 1 system Checked pressures. Checked voltage and connections throughout. Checked amp draw. Checked capacitor. Cleaned coils. Checked airflow. Cleared drain line. Recommended and put in pan strip. Unit is working properly at this time. Mr Staton wants to purchase/renew SA at a later time
Run circuit for unit
Scheduled Maintenance 2019 Lennox / 2011 Carrier
Replaced disconnect, whips, and breakers.
Condensing Unit #2 Making Loud Noise 2019 Lennox warranty less than 1yr.
Replaced breakers, marked heat kit, and rerouted wire for air handler
Relocated AH disconnect, replaced whip, breakers, and installed gfi receptacle for air filter system. Marked heat kit used.
Preformed service call on ruud system
Replaced whips and breakers. Need 2- 4kw heat kits. Wire size will not support 5kw. I let Mark know.
Warranty service call.
Install 40 amp classified breaker One 6 foot three-quarter wheep