Work inside the residence. TG arrived on time in a clean clearly marked truck. Neat appearance. Reviewed work order, installed two type-2 Sieman surge protectors (one to the HVAC circuit another to the house panel box), installed new can light, new ceiling receptacle over fireplace for natural gas alarm, and a new receptacle to existing switch. Repaired bathroom light circuit that original electrician could not. Politely led walk around of completed work. All work neatly finished. All work areas clean. Bill exactly as estimated. The A-HVAC+ Electric phone number remains on our refrigerator.
Response from A+ Heating & Cooling- Electrical:
Thank you, Don, our technicians like to work diligently and check all ends before jumping to conclusions to make sure we get to the bottom of the issue, so you can enjoy the air conditioning.