Very polite. Neat work
Response from A+ Heating & Cooling- Electrical:
Hi Floyd, we understand the importance of cleanliness, especially given everything going in the world today.
Demand Client has not received maintenance since installation
Condenser fan motor.. complete. Mrs Stevens will call the office to make payment she is at work.
Service call. 2012 Goodman package heat pump. Needs condenser fan motor.
Demand no cool
Replaced whips, installed disconnect and circuit for AH and replaced breakers. Disconnected circuit for old furnace
WARRANTY GAS VALVE
Installed WARRANTY BLOWER CONTROL BOARD, FLAME SENSOR AND SPARK IGNITER on two year old gas package unit. Started system. System goes through proper sequence then gas valve clicks and shuts power down to the board. Checked over all safetyâ€™s and new parts installed. Clients gas valve is shorted, office to order a new gas valve with LP conversion kit. Control board, spark ignitor, flame sensor
Demand no heat
No heat both gas packs
Performed prepaid maintenance. See notes
No heat in kitchen
Replace blower motor
Unit not cooling freezing Please order quarter horse 1075 to 220 blower motor