Very polite. Neat work
Response from A+ Heating & Cooling- Electrical:
Hi Floyd, we understand the importance of cleanliness, especially given everything going in the world today.
Goodman gas package Checked systems and found on one system the 5 amp fuse on control board was not plugged in properly. Corrected fuse and started system. Unit is working properly at this time. Second system had no power at unit. Breaker was not tripped. Turned breaker off and back on and system started. Units are working at this time.
2014 Goodman system maintenance
Performed routine maintenance on a Bryant package unit. Checked filter, checked thermostat, checked elements and blower amps, checked the evaporator coil, checked drain pan and blew out the drain line, checked/tightened electrical connections, checked capacitor, checked fan and compressor amps, checked pressures and reversing valve, cleaned condenser coil
Performed routine maintenance on a Ruud/Mortex system
Performed routine maintenance on a 2014 Goodman package system
Demand call on a 2001 ICP product with a mortex system. Found the blower motor not responding motor had a bad 10 ÂµF capacitor. Replaced bad capacitor blower motor is now operating normally. System has several condition issues heavy corrosion has taken over the evaporator coil. System is cooling OK at this time.
4 Goodman system Estimate for duct cleaning sanctuary has 18 to 20 foot ceiling Will require adequate ladders. 2415+ tax
Start capacitor 1 mfd replace
Going to try to get back into the home
2011 Bryant duel fuel bad vent motor capacitor 1 mfd
Install three UVC light kits 2 in the sanctuary 1 in the fellowship dining room Gave Mr. Brown a estimate for silver cool club membership for systems 450+ tax
2011 Bryant Duel fuel package unit super tune up
Performed routine maintenance on a goodman 5 year old system
Checked install. Ready for inspection
She bought a 15 seer 3 1/2 ton Ruud system