Replace blower motor
Unit not cooling freezing Please order quarter horse 1075 to 220 blower motor
7 lbs r-22, leak search, burners, & compressor are needed at minimum to get back up and running. A+ highly recommends that the system be replaced for best value. Compressor has been replaced system was put on a nitrogen leak test then put on a deep vacuum recharge with factory 7 pounds unit is working at this time on the cooling side
No one answered the door
2015 Goodman package unit- checked system amps checked blower motor and blower wheel checked evaporator coil and clean evaporator coil checked wiring checked fan motor checked compressor checked contactors and capacitors checked float switch checked heat strips checked condenser coil and clean condenser coil. replaced weak capacitor which was covered by warranty.