Client was unavailable at this time.
2016&2017 Goodman 2 system maintenance
Performed prepaid maintenance on 2017 split system And 2016 package unit
Check system get a temperature difference I got 17Â° across the coil got 68Â° going into the return 51Â° coming out of the supply check pressures pressures look good blower motor is running good checked coil was not icing unit is doing all it can do customer is asking for 66Â° thermostat showing 70 in the house return is pulling in 68
Stat was wired wrong rewired unit is working now also blower motor was making a lot of noise fixed that issue motor sounds right
For routine maintenance on one year-old gas pack Goodman system check flu checked safeties check burners checked blower motor checked gas valve checked inducer draft motor check vacuum switch performed routine maintenance on one year-old heat pump Goodman system checked heat strips clean coils checked blower Motor checked condenser motor checked compressor checked contactor checked capacitor checked temperature units are both running OK at this time