Joshua was friendly, detailed in is work and explained everything well. Showed me phots of everything he had inspected.
Tech found problem, appears parts under warranty. Good communications
BN was prompt and did a complete and through count of the ducts and returns. He provided us with a price that was higher than expected, so we will need to shop this service around for now.
Scheduled regular maintenance and a few days before they came we lost our compressor. They were able to get the replacement and fix our a/c the day before we left for vacation. Thank you guys.
Kevin was professional, knew what he was doing, and overal nice guy.
Appreciate his prompt service
Josh was my service tech...very polite and courteous.... explained everything he did... 🌟🌟🌟🌟🌟
Scott was professional, friendly and knowledgeable. He is an A+ asset.
When i arrived unit was only running in cooling. Performed troubleshooting diagnostic and found tstat bad . Return for parts under warranty . Job completed
Ruud 1.5Ton 15Seer Heat Pump Split System.
Lennox/Ruud 3Ton 15Seer Heat Pump Split System.
Performed routine tune up. Inspected and confirmed all major components and safetyâ€™s that I can physically get to was operating properly. Disinfected and deodorized the indoor coil. Pressure temp relations are normal. Job completed unit is running properly at this time . H/o will be sending check
2016 Trane Checked system and found unit to be out on low pressure. Found oil residue by checked valve on suction line. Adjusted Schraeder valve and checked for leak with bubbles. System has leaked refrigerant before and has already had a leak test. Added 1 pound of 410a. System is heavily corroded on the outdoor unit. If refrigerant loss occurs again replacement is advised.
Assisted Chris with indoor coil. Job completed
Replace evaporator coil. Pressurize and leak test system. Pull vacuum. Charge per manufacturer specs.
Performed routine maintenance on a Goodman system 2019
Performed routine maintenance on 3 systems Comfort specialist is scheduled to come out to give a quote for the downstairs unit which is a 2007 trane unit. Other units are a 2020 Ruud and a 2018 Goodman
Out door condenser leaked all refrigerant out. Condenser has been replaced and charged. Running properly. Job completed. Customer stated heâ€™ll pay w/melody.
Helped BG with condenser coil
Performed routine maintenance on 5 systems
2019 Ruud Leak search on Ruud system. Found leak at high pressure switch on outdoor unit. Will have to order part and return.
I preformed a maintenance on 2 Ruud units. Indoor units: I checked amps on the blower motors and heat strips, I checked the electrical wires and connections, I checked the drain pans and drain lines, I checked the float switches, I checked behind the disconnects. Outdoor units: I checked amps on the compressor and fan motor, I checked the capacitors, I checked around the contactors and the boards, I looked into the units for rubbed wires and rust, I cleaned out the bottom of the units, I vacuumed the drain lines and washed the units down with water. When I started to check the outdoor units, I noticed the upstairs outdoor unit wasnâ€™t on, I took the door off and noticed a flashing code telling me low pressure, I checked the two valves, I applied my gauges, I pushed in the contactors for a brief second, I then concluded that the unit had 0 refrigerant, Other than the upstairs outside unit everything is working properly, I spoke to both the homeowners and they would like it to be taken
2019 Ruddâ€™s 2 systems Checked pressures. Checked voltage and connections throughout. Checked amp draw on compressor and fan motors. Checked capacitors. Checked safety switches. Cleared drains. Checked condensate pump on downstairs system. Put pan strips in both systems. Downstairs system is corroding at the outdoor unit. Gave estimate for membership and gave estimate for corrosion grenades. Units are working properly at this time.