Pre paid maintenance
Leak searched system again with nitrogen. Found small leak at schrader valve and tighten. Replaced filter drier. Checked system with nitrogen. Pulled vacuum and charged system with 8.65 lbs of R22. Also, replaced the contactor no charge.
Super Tune Up with brochure. Found system running on heating elements and no refrigerate. Leak checked with nitrogen and found no leaks. System has not ran in years so possible some has removed the R22 refrigerate. **Will need to come back to replace filter drier, pull vacuum, and add 7lbs of R22 refrigerate. 1 system: 2007
Diagnostic call. Entered clients information in the system. Found wrong size blower capacitor installed for the blower motor. Installed a 7.5 mf capacitor. Started system and checked over entire system. System has a high suction pressure and an excessive discharge temperature. These are indicators that the valves in the compressor are starting to go bad. System is operating, client will continue to monitor the thermostat and call us if thereâ€™s any problems.
Warranty service call.
Super Tune Up **Quoted UV light install 1 system: 2014
Warranty- No problems found with equipment, problems found with existing duct system: Leaking multiple areas supply side & pinched 18 in or 16 in return side flex. Recommended replacing entire duct system or sealing leaks & fixing return.
I checked the system and thermostat. I also replaced the thermostat as a precaution. See notes
Service call: Found System low on refrigerant with coil partially frozen, Verified blower operation, Preformed stage 1 leak search. Result: No leaks present or is a micro leak that is not detectable. Charged system with 2lbs R-410a Refrigerant & checked ductwork. Ductwork work is in incredibly poor condition & leaking lots of air &is poorly insulated. Recommended changing ductwork if more Cooling is desired. Signed up for silver Membership Valid 5/29/19-5/29/20 please put into system
Warranty 1st year parts and labor: Customer says Unit running all the time & it was over cooling even though the thermostat was reading 76 and it was set to 76 but it never shut off per Mrs - Checked equipment & Verified Refrigerant Pressures, sealed hole in wall behind thermostat & Change some of the configuration settings in the thermostat like 5min delay. FOLLOW UP/LEAD: Told Mrs that her other unit for the upstairs is not working very well and she should probably have it replaced, she understands this and will consider her options, please call to try and set up price quote for 1 1/2 ton split system