Diagnostic call. Entered clients information in the system. Found wrong size blower capacitor installed for the blower motor. Installed a 7.5 mf capacitor. Started system and checked over entire system. System has a high suction pressure and an excessive discharge temperature. These are indicators that the valves in the compressor are starting to go bad. System is operating, client will continue to monitor the thermostat and call us if thereâ€™s any problems.