They were all professional and very nice. Explained what they were doing and or did. Cleaned up.after themselves, couldnt even tell they were here. Great service!! Thank you.
Response from A+ Heating & Cooling- Electrical:
Thank you, John, we like to provide our customers with excellent service through hard work, explaining procedures, so the client understands the work being done and keeping a clean workspace!
2019 system was determined to be very slightly overcharged with refrigerant. No further issues were detected with the equipment at this time. Due to the heavy volume of leaves falling inside of the condenser, it is necessary to install some form of protection in order to maximize the life of the equipment. Leaves in the bottom of the condenser hold water, which rust and corrode components, such as the condenser coil at a rapid rate over time.
2019 systems are in good working order. No issues were detected with the equipment at this time. Motor in downstairs condensate pump was found to be near failure. Replaced condensate pump. Also installed germicidal UV light downstairs.
Replaced disconnect, breakers, and whips. Replaced keyless fixture and installed gfi
Replaced whips and breaker
Replaced heat kit
Changed disconnect, breakers and whips. Double install. Need 3 key heater kit for upstairs air handler.