A+ always is there when you need them.
Superior, efficient service from a friendly, personable technician. Would definitely recommend!
Austin did a great and very efficient job! He was very thorough in checking out our system for it's semi-annual maintenance check. We appreciated his courtesy and his dedication to making sure our system was running at peak efficiency.
Auston was very personable and professional. He serviced our unit and explained everything as he went along. I wanted him to look at my vents and he checked them out for me.
He was early which was good but not in the time frame mentioned. Lucky i was here. He was very knowledgeable and took the time to explain things. He didn't really find anything wrong except for us to open all the inside doors so air can circulate and with metal building we still can't get the temperature below 80 degrees. He had soome good suggestions. We had this happen before and it was resolved and we did all the things he said to do but it hasn't helped. maybe because of the very hot days it is affecting they system. Me mentioned that our ducts might need cleaned but i can't afford that. All of your technicians are really good.
Condensation line was clogged and secondary pan was full of water clean condensation line out with vacuum and secondary pan all systems are running at this time
Convert fluorescent lighting to LED
Performed routine maintenance on a trane unit 2014
Performed $59 super tuneup on a 2013 carrier heat pump split system. Overall the system checks out I did find the capacitor running week on the outdoor unit this was a 40/5 ÂµF. Replaced bad capacitor found on the indoor evaporator coil is starting to corrode pretty heavily. There are no leaks present at this time . The coil is something we will need to keep her eyes on for future failure.
16in zone damper Pictures in service titon Reschedule until 2 techs can come out.
Customer wanted his ductwork looked over to make sure there was no holes in it. I did not see any at this time. The ductwork appears to be in pretty good shape. Left customer a message we do have his credit card on file but the expiration date and the security code is missing in our dispatch .
Checked all electrical numbers and Freon pressure cleared drain line Would recommend a duct cleaning
New install 2021 Goodman system SS2 tripped clean and flush condensate drain
Drain line full of sludge not allowing water to flow out fast enough cleared drain line unit is working properly at this time
2014 Ruud system clean and flush condensate drain remove water from secondary pan
2015 Heil system noise homeowner is hearing coming from blower motor bearings are bad will need to be replaced
2015 Lennox XP21 system zone board had malfunction locking system out checked over sensors, wiring reset system. zone board and unit are both communicating and working properly pressures are good
2016 Carrier Checked system and found compressor short cycling. Pressures are good. Amp draws are good. DATs sensor at zone board is faulty, was showing a 31 degree temperature while gauges showed 50 degrees. Disconnected sensor, will need to order and replace
Performed routine maintenance on a Goodman package unit.
2017 Goodman Owner had stated the tstat would go blank and then come back on. Checked drain line and it is draining good. Found Louvers on access door to air handler and cover on AHU heavily restricted with debris. First pressure check had a 34 degree evap coil temperature. After cleaning debris out from louvers evap coil temperature was at around 50 degrees. This restriction was causing the unit to ice up and tripping AG2. Advised owner to keep louvers clean to allow proper airflow.