Performed $59 super tuneup on a 2013 carrier heat pump split system. Overall the system checks out I did find the capacitor running week on the outdoor unit this was a 40/5 ÂµF. Replaced bad capacitor found on the indoor evaporator coil is starting to corrode pretty heavily. There are no leaks present at this time . The coil is something we will need to keep her eyes on for future failure.