great job done
We will ask for Lionel Long the next time we need service. Very knowledgeable. Pleasant person.
Very nice tech. Chris was great.
The technician that came out was very courteous and worked quickly to service our system.
I appreciated the fact that the company texted us that the technician was on his way plus his picture was included. Joe was very friendly and fixed our unit promptly. We were very satisfied with his work. Thank you Joe!
Call A+ Heating and Cooling!! They provide the best service I have had.
Found low-voltage fuse blown on fan control board the orange wire going out to the compressor or shorted replace wire with green wire
Breaker feeding the airhandler is bad 60 amp double pole breaker needs to be replaced Itâ€™s on the outside of the house beside the porch
Clean pressure switch and lines cleared water and blew out drain again system is working for now.new install set as soon as possible.
2019 Goodman system 3/4 Blower motor is bad will have to be replaced also there is an electrical issue at the disconnect pulled disconnect still had 240 going to the unit.
2016 Ruud system replace defrost control board
Replaced bad over limit switch on a 10K W heat kit. System is operating at this time.
12 inch 2wire damper and motor Old Bryant gas furnace in need of replacement comfort adviser coming out 1 PM today
Demand call on a 30 year old mortex furnace. Found the over limit switch on the 10K W heat strips to be faulty and needs to be replaced. Return for parts has been put in for this as well as the estimate.
2016 Ruud system System was stuck in defrost cycle kicking unit out on high-pressure reset board forced manual defrost cycle unit is working properly at this time
2015 Goodman 2006 Bryant gas furnace 12 inch damper assembly needs to be replaced
2019 Ruud system maintenance 10/10/10 customer
2015/2019 Lennox systems maintenance
Super tuneup on a 2013 goodman . Customer signed up for membership . System is working good no issues found .
2015/2020 Ruud system Downstairs unit 2015 excessive water around condenser coming from system defrost cycle, checked over both systems no issues detected. 10/10/10
Performed maintenance in heating Replace uv bulb Sold 2 air bear