Auston did a great job and we appreciate his excellent service!
From the very beginning, service has been exceptional. After using A+ for a repair to our unit right after buying our house & then deciding to go with them for 2 new unit, their team has been the greatest. We just had our one year maint. inspection & Kevin was the technician. He arrived on time & was very professional, friendly and seemed to be thorough. We love our new units and the A+ team that installed and has been servicing. Thanks so much for a great experience.
Great knowledgeable technician
Response from A+ Heating & Cooling- Electrical:
Hi Elliot, thank you for sharing your experience with Swift Services. We take the time to explain what we are doing while performing services. HVAC units are some of the most complex systems in our homes, so it is important that our customers understand what and why we are doing.
Call back on a 2016 Rod heat pump split system with a mobile unit inside. Need to return recovered all refrigerant put system on nitrogen purge put system on a vacuum then recharge with factory 410 A There will be no charge for any of this once this process is done we will diagnose to see if there are any further issues
Demand call on a 2016 Lennox heat pump split system. Found thermostat blank ,system was off on a water switch. Cleared drain ,cleared the cup ,system is now operating normally. Customer would like a copy of last invoice as well as this invoice on paper
2006 Goodman Checked system and found several issues. Low pressure. Oil residue in drain pan. Weak capacitor. Unit is running at this time however it is not efficient and has a leak. Owner requested comfort advisor to come out about replacement.
Checked install. Need 2 co2 detectors in house. Ken to return later to install
Changed breaker for Ac Changed breaker for heat Replaced wire in whip on Ac
Performed routine maintenance on 2 Ruud systems
Installed a condensate pump.
Water was again found in the SS2 float switch. Cleared drain line again and adjusted the straps for maximal drain grade. If issue persists in the future a condensate pump will need to be installed in order to evacuate water from beneath the home.
2016 Ruud system braise repair leak on high pressure switch stem add 6 pounds 410a
Outdoor unit was not running due to the SS2 switch had water in it from the condensation line having clogged up clean condensation line with vacuum All systems are working properly at this time Down stairs system
2/2020 Goodman system Upstairs clean and flush condensate drain system is working properly
Condenser coil is leaking will have to be replaced Comfort adviser scheduled to come out tomorrow around 1 PM
Demand call on a 2006 train gas furnace. This furnace is dual stage and has a full variable speed motor in it. The blower motor is bad and needs to be replaced. Customer has an appointment to speak to a comfort adviser on Friday at 10 AM.
2016 Trane system Dirty sock treatment, clean evaporator coil. clean and flush condensate drain line
Checked all electrical numbers and Freon pressure cleared drain line system is operating properly at this time