WARRANTY TEMPERATURE SENSOR
Miss Susan wants to reschedule for Thursday morning
Aux heat not working
Replaced whips, disconnect, removed feeder for AC that was tapped under loadside of meter, rewired circuit to breaker in main panel.
PR0 5000 T/STAT AND DEFROST BOARD
Check breaker in main panel found wire loose on one leg of two pole breaker titan breaker Forced unit into defrost breaker did not trip also tighten logs at pool disconnect and that unit
Super tune up
Performed prepaid maintenance. Homeowner will call the office and renew membership.
Low air flow in back room and bathroom
Replaced whips, breakers, re-ran AC circuit, and helped installers set equipment
Preformed service call on Goodman system
Unit not working