Response from A+ Heating & Cooling- Electrical:
Hi Wayne, thank you for sharing your recent HVAC service with us, we are glad to hear you received Great service.
2020 Daikin mini splits 2 systems Checked pressures. Checked voltage and connections throughout. Checked amp draws on units. Cleaned coils. Cleaned filters. Units working properly at this time.
This is a remodel it has no system no ductwork nothing so we have to put all new ductwork new system everything and Iâ€™m going to send him a quote on it
Was unable to detect any issues with the equipment at this time. System is in good working order. Increased the airflow due to the volume of the ductwork.
Installed ultra violet light.
Replaced breakers, helped Chad set units in place.
Installed subpanel and circuits for mini splits