He was very nice, did his work. Very satisfied
Response from A+ Heating & Cooling- Electrical:
Hi Diane, thank you for sharing your recent AC service with us, we are glad to hear you received Excellent service.
Need to install 6 space outdoor panel and subdivide AC and heat sections of package unit. There is 6 stranded copper run to the unit. Will need 60 amp GE breaker, 40 amp Homeline and 25 amp Homeline breakers. Will let Sam to know to hold off on inspection
Added circuit for closet light switch and install customer supply block
Maintenance on a 13-year-old miss matched heat pump split system upstairs with a eight-year-old packaged unit for the lower level
Need to send Mark back with me to see if we can relocate the thermostat
Gave to Lionel per John
Electronic leak search found leak on expansion valve tighten fittings stopped leak add 1 lb 410a
6 systems 1 mini split Checked pressures. Checked voltage and connections throughout. Checked ampndraw. Checked capacitors. Cleaned coils. Checked airflow. Changed customer provided filters. Cleared drain lines. Units are working properly at this time.
Air filter was very dirty had Miss Doris remove it. Add 1 pound refrigerant system is working properly should hold till she gets over Covid we can come back and do leak search
Found system 2 pounds low on refrigerant. Added 2lbs to get her cooling Miss Hart Is very sick right now when she gets better and out of quarantine will need to come back and do a thorough electronica leak search inside, cannot do anything outside today it is raining
Dispatch to the church there is nobody here to let us in they will need to call the office and reschedule for when they are going to be here
Check system and found loose connection at the thermostat fixed loose connection and added 1 pound of 410 A system is working good now checked refrigerant pressures and checked blower motor
Check system found system low on Freon 410A found leaks in the evaporator cool but we need to find out if itâ€™s under warranty before we order a new one
2020 Rudd system adjust refrigerant to bring pressures up to Specification silicone around kitchen vent to stop condensation.Condenser pad was not changed at installation please contact homeowner to resolve