He was very nice, did his work. Very satisfied
Response from A+ Heating & Cooling- Electrical:
Hi Diane, thank you for sharing your recent AC service with us, we are glad to hear you received Excellent service.
2020 Goodman system has not satisfied since it was installed I did leak search found no leaks add 2 lb 410A
Replaced breakers and disconnect
Replaced breaker for outdoor unit. Everything else was up to code.
Check system checked blower wheel and blower motor checked evaporator coil and condenser coil and cleaned all components and make sure system was working fine system is a 2012 package unit and everything is all right
Removed paneling around panel box, ran new circuit to indoor unit, put paneling and trim back up, replaced disconnect, replaced breakers, and replaced whip.
2019 Ruud system maintenance
Lights dimmed and breaker tripped yesterday due to frog shorted out the contactor
Demand no cool
Check system checked blower motor and blower wheel checked evaporator coil and condenser coil clean all components installed a hard start kit check fan motor and compressor compressor is running high amps check refrigerant levels they are low it is a r22 System system needs to be replaced
Performed prepaid maintenance. 1 system 2019 package unit MN/GPH1448M41AB SN/1811285038 see notes
Clean and check 6 systems 1 mini split
Replaced burnt outlet in kitchen and fix wiring in ceiling fan
Called client was informed this is no rush to let them know when in the area again.
Performed prepaid maintenance.
troubleshoot and repair lights in master bedroom not working Tech found issue with neutral wire under house in Junction repair neutral lights are working properly at this time