2019 Lenox 1 system Checked pressures. Checked voltage and connections throughout. Checked capacitor. Checked amp draw. Cleaned coils. Checked airflow. Cleared drain lines.
Did not call after hours. System is working fine.
Warranty service call. Bad TXV on the heat pump.
Change call from callback install to warranty call. Plastic condenser fan motor shroud under metal top was vibrating really bad. Fixed connection. Restarted unit. System is not making loud noises anymore. Entered pinned notes. Emailed client copy of invoice.
Performed duct cleaning.