Always on time, competitive pricing and considerate of any issues. A ten year customer.
Great service by tech
The day before Thanksgiving my package Unit on the roof of my condo went out. A team came that day and gave me the bad news , it could not be fixed, replacement was necessary. A long story short, my new unit was installed with a crane no less without ruining my holiday or my bank account! Thanks A team!
I have a trust with A Team. They do what needs to be done; and don't take advantage.
The A-Team responded quickly to my service request, and the service technician, Greg, was friendly and very professional, quickly resolving my AC problems and clearly explaining to me the costs associated with the service. The A-Team and Greg were indeed my heroes on a hot summer day.
Jeff, arrived in an on time manner (called 30 minutes prior to actual arrival). He wore foot coverings to protect our floors. While performing routine semi-annual service, noticed three necessary repairs/upgrades. Discussed cost of each. Prices sounded good. Had parts/supplies with him and immediately did the work. No need to schedule another visit. Did the work right then. I look forward to the next semi-annual visit by Jeff or another team member. Jeff, keep up the great work! You are an asset to your company. Thanks. Ed and Colleen
We've been using A-Team for years and they are top quality people, year in and year out. Product, Services & pricing are great but mostly they are just good people that care about the quality of their work and about their reputation and it shows.
Working on a draft inducer motor for Rheem system
Repair line set on a carrier unit
Added 2 lbs R-22 to a a Carrier air conditioner with Goodman coil.
Air conditioner tune-up on a 5-ton Lennox system with two zones
Air conditioner maintenance on a Carrier heat pump system
Air conditioner maintenance on a newly-installed Rheem system. Found bad 10 inch motorized damper. Need to reschedule to replace motorized damper.
Air conditioning maintenance on a Friedrich/First Company closet package heatpump system. Changed 16x25x1 filter
No cool on a horizontal Amana system. Had impacted filter and dirty condenser
2 system air conditioning tune-up on high efficiency Trane 14 seer 410a systems. Recommended replace both capacitors and acid wash both condensers.
Two system air conditioner tune-ups on Goodman systems
No cool on a Trane R-22 system. Found blown 5 amp fuse, replaced, and air conditioning now operating properly.
No cool on a First Company water source heatpump unit. Low on R-22, previous leak found in evaporator coil. Added 4 lbs refrigerant, system now cooling. 63� supply air, 81� return air.
Air conditioner tune-up on a Lennox R-22 heatpump system. Changed 18x20x1 filter.
Found refrigerant leak while working on Amana air handler. Need to return to perform leak repair and recharge with 410a.