Marco and Alec were fantastic on the new install. Very professional, thorough and efficient!
Always on time, competitive pricing and considerate of any issues. A ten year customer.
Great service by tech
The day before Thanksgiving my package Unit on the roof of my condo went out. A team came that day and gave me the bad news , it could not be fixed, replacement was necessary. A long story short, my new unit was installed with a crane no less without ruining my holiday or my bank account! Thanks A team!
I have a trust with A Team. They do what needs to be done; and don't take advantage.
The A-Team responded quickly to my service request, and the service technician, Greg, was friendly and very professional, quickly resolving my AC problems and clearly explaining to me the costs associated with the service. The A-Team and Greg were indeed my heroes on a hot summer day.
Jeff, arrived in an on time manner (called 30 minutes prior to actual arrival). He wore foot coverings to protect our floors. While performing routine semi-annual service, noticed three necessary repairs/upgrades. Discussed cost of each. Prices sounded good. Had parts/supplies with him and immediately did the work. No need to schedule another visit. Did the work right then. I look forward to the next semi-annual visit by Jeff or another team member. Jeff, keep up the great work! You are an asset to your company. Thanks. Ed and Colleen
Service Agreement Fall tune up on Rheem heat pump with 14x20 wall filter rack
1 system tune up on a trane system heat pump
Installed 2 full systems w/ 16�25�1 filter rack + in line switch
Installed uv Light + r/a box w/ 16x20x4 media filter
Installed full systems
Installed full systems + drain pan w/float switch
Doing a leak search on a Goodman 16 seer heat pump system fixing fireplace gas leaks
Checked heat on Carrier mini split system. Completely out of R-22 freon. Recommend new air handler and heat pump.
Repaired water leak
REPLACED THE DRAFT INDUCER MOTOR AND BLOWER CHANGED 14X25X1 FILTER
Installed circuit board
Installed 1 1/2 ton wall unit. New duct work and float switch,
Heat pump was low on freon. Added 6 pounds of 410A refrigerant.
Installed 3 1/2 ton 16 seer Rheem Furnace.
Fan wiring bad on a retro air 1 and 1/2 ton heat pump