Have any feedback for us? We'd love to hear it! Call us at (405) 888-5253 and let us know how we are doing.
Good experience. On time, received text prior to technician arriving with pic so we knew who to expect. He explained the service, provided insight into condition of our units. Kressy was courteous, respectful, responded adequately to our questions, we were very satisfied with the overall process and technician
Had a problem, Kressy came out diagnosed it and fixed it.
Friendly Technician...took time to listen to my concerns and made solid recommendations.
Fabulous! Listened to me and found the best price for my needs. Very intelligent and responsive
Kressy was exceptional, friendly, professional and explained everything very clearly.
System frozen on arrival Once thawed I found leak with leak detector and showed customer Also furnace flue pipe is broken and need and new 4â€ 90 and connector North side ac capacitor 45/5 out of tolerance reading 35.95/4.30 needs replaced South side ac outside of fence 35/5 capacitor is out of tolerance reading 32.13/4.92 recommend replacing New coil and txv installed and working properly I installed new capacitors And I fixed vent issue System is on and cooling well Will take awhile to get temp down considering it was 89 degrees when system was started back up
Compressor is shorted to ground. R-22 system needs replaced with 410a heat pump 5 ton.
Installed new coil and txv Adjusted charge System is cooling very well
Both systems checked. Gym is set at 72 cooling, and cycling off. Event side was turned up to78- 76 in the room turn down and checked and it is cooling as well.
New condenser motor and capacitor.
System is cooling to the best of its abilities with no issues Return temp 74 degrees Supply temp 53 degrees Thermostat is reading 73 degrees 21 degree temp difference is excellent Very efficient
Condensers were really dirty causing compressors to run higher amps than normal but after I washed them out both compressors amps dropped like they should Changed filters Both systems cooling efficiently Customer signed up for service agreement and purchased replacement filters
AC upstairs not cooling. Found leak in evaporator coil. Customer will be replacing coil at end of year. Added 11 lbs 3 ounces of Freon to system.
Drain had clogged up again, I blew out the main drain to the deposit area yesterday but I didnâ€™t blow it out towards the coil and thatâ€™s where our clog was. I also poured bottles of water into coil to be sure that main drain was draining
5uf capacitor on ac for fan motor is out of tolerance reading 3.57, I recommend replacing 15uf blower capacitor is out of tolerance reading 13.48, I recommend replacing System low on r22, found leak in coil and took video showed customer Customer will likely buy new coil but wants to wait until heâ€™s back from vacation to make the decision
3 car garage
Blower motor broken arm, needs new motor New motor installed and system is cooling
Wireless thermostat found and working
AC outside running constantly. Found thermostat is defective and causing the issue with the outdoor unit.
Capacitor was out After installing capacitor system wasnâ€™t cooling correctly and I noticed that the system is out of refrigeration Customer elected to just add r22 system holds 6.25 lbs I added r22 and system is cooling well for now it will continue to leak