Have any feedback for us? We'd love to hear it! Call us at (405) 888-5253 and let us know how we are doing.
Very impressed with Jesse! He greeted me very friendly. He quickly and very throughly explained the issues of the problem with my Mom's heating system. He spent a little additional time to insure the system was working correctly. I am very impressed and highly recommend Jesse Eskew. Jerry King
Fast, friendly, and convenient
Above and Beyond has always provided phenomenal service with the highest integrity!!!
They came the afternoon of the day I called. I was so happy to receive prompt service.
Great job, great price!
Arrived early and very knowledgeable
Found that wind is coming backward down through the flue and blowing out the flames on both units
found a bad roll out switch.. part will have to be ordered
24volt fuse was blown upon arrival Changed fuse, found loose wire connections on control board, fixed loose wire connections and heater was working when I left
Cleared pressure switch hose, pressure switch is sticking open at times, high limit is bouncing around which means itâ€™s getting worn out but itâ€™s still working right now, I recommend replacing the high limit switch and pressure switch because I canâ€™t guarantee how long they will work Installed new pressure switch and high limit control System heating well when I left
Checked roll outs (3); checked high limit (1), checked igniter, checked pressure switch and ports, checked blower amps 5.8, checked system for CO from inside of coil and got 1ppm which is not a problem, ran system without thermostat muiltple times and it worked just fine, then I ran system with thermostat and it worked as it should System is running as it should
Bad inducer motor Board sending 120volts to inducer motor and motor is not coming on
Drain had fallen apart at system in 2 different spots... reconnected drain and poured water to ensure good operation
Replaced both roll out switches Heater running when I left Customer said heater has been running no problem
Bad hot surface igniter System sending 120volts to igniter and igniter wouldnâ€™t glow Installed new igniter and system fires right up Checked limits (3) all good Checked home for CO because system is over 15yrs old found 0ppm
Checked coil and blower for obstructions that would cause the smell and they were both clean and clear Sprayed coil cleaner on coil Filters are dirty and need replaced homeowner has filters and husband will replace Ran system for 15-20mins and smell never came back Took videos of coil and showed Jennifer
South condenser 45/5 capacitor is reading 0 needs replaced Changed filters 20x30x1 (2) Washed condensers, checked compressor and fan motor amps Started both system and checked charge the best I can Reconnected flue pipe on upstairs system Blew out both drains
System was heating when I got here was 70 in home and thermostat was set to 70 System has been running for 2months without filter per customer Blower capacitor is 5uf and is reading 3.7 I recommend replacing but system is still running Cleaned flame sensor, checked igniter, limits, pressure switches Blower compartment is really dusty Coil is a little dirty, in my opinion not dirty enough to have it pulled and cleaned Cycled thru system multiple times to ensure it was working correctly Filter size 30x12x1 customer said he was gonna get one first chance he got Checked temp rise and 68 from return and 112 from supply which is within manufactures specs of 40-70 Drain is flowing as it should Checked combustion motor amps 2.1 and max is 2.35 System is heating well right now if problems start again get us out ASAP while problem is occurring
Cleaned flame sensor, checked blower capacitor, igniter and found that thermostat was not sending call to heater to turn heat on... bad thermostat Replaced thermostat and system was heating when I left
Reconnected flue pipe to system used metal tape and screws to secure pipe.. cycled thru system multiple times to ensure good operation