Have any feedback for us? We'd love to hear it! Call us at (405) 888-5253 and let us know how we are doing.
He's great! He was extremely helpful. Thanks you.
Great service. They did what was asked quickly and at a fair price.
I called on Thursday evening and someone came by noon on Friday! They were professional, friendly, efficient, and priced right! Thank you!!
Kressy/Tech did great job/ very prfessional & knowledgeable giving us a quote for new ac/ heater and answering my many questions! Great Service & information and very good price quote!!
Installed new t4pro thermostat Fixed drain Found leak in coil with leak detector Blower cap 10uf reading 9.37 +/- 5% capacitor is out of tolerance System has no filters installed Ac and heat both come on 40/5 capacitor reading 39.64/5.13 Condenser fan amps 1.24 max per data plate is 1.50 Compressor amps 7.06 max per data plate is 12.2 System low on r22 House has no water so I canâ€™t wash condenser I recommend replacing system bc itâ€™s 10yrs old and has not been taken care of Replacement of full system New air handler and heat pump comes with 10yrs parts and 10yrs labor warranty Will replace box under unit do to water damage Bring return plenum to match Will install surge protector on heat pump to prophecy compressor and control board System comes with new thermostat Filters needed 2-24x14x1
Combustion motor not running as it should has bad bearings needs replaced new motor installed and working great Control board has a short in it causing the ticking sound Recommend replacing but customers wanna wait due to system working ok Checked home for CO 0ppm
114 harvest Bad 60amp breaker Breaker replaced and system is operating
Cleared clogged drain and added algae tablet to drain pan Filter was dirty so I changed filter with customers filter Drain flowing
OG&E tune up
New furnace, coil, condenser, and thermostat System comes with 10yr parts and 10yr labor warranty
OG&E Residential Tune-up on customer's home.
All returns are in stalled all door returns are installed except 174 no door used 20 feet of 4 in flex duct Customer needs you to find supply grills inside measurement 6x18 and quoted price.
Bad compressor Tries to come on but is mechanically locked 2ton condenser or new compressor is needed
Charged system and its cooling for now
Sealed txv Sealed tear in line set armaflex
Installed new thermostat and lowered blower speed to help with master return noise
Old mercury thermostat finally stopped working. Replaced thermostat with Honeywell pro thermostat. Check refrigerant charge and was system was low. Added 1 lb of R-22 to for system efficiency and to allow system to run without excessive heat build-up.
OG&E tune up
New furnace, coil, condenser, and thermostat comes with 10yrs parts and 10yrs labor warranty Strap duct work the best we can