Have any feedback for us? We'd love to hear it! Call us at (405) 888-5253 and let us know how we are doing.
Kressy was awesome, he was right on time and did an excellent job getting my air conditioning up and running in no time. Glad I called this company.
The technician was very knowledgeable and very nice. He really made us feel like he cared about our home and HVAC and wasn’t there to try and sell us something we didn’t need. We will definitely be using this company and hopefully technician for all our HVAC stuff for as long as we live in OKC.
The reminder system is helpful and showed a picture of the technician that would be coming to the house. He was knowledgeable and was able to troubleshoot quickly. We had resolution quickly and I was able to go on with my day.
Great Service and price was great!
Installation of new Lennox 18 seer high efficiency dual fuel heat pump system. #NR
Installed vent covers on downstairs registers per homeowner. Replaced thermostat and heat pump is operational. Second stage heat, emergency heat, is set on a 15 minute delay in thermostat. Properly installed connector on whip for heat pump at disconnect to secure as required. Noticeable lack of air flow in laundry room and downstairs bathroom. High flow grilles installed has helped air circulation. Heat was turned on to 80 degrees with outdoor temperature of 57 degrees. Temperature heated up in home to satisfy thermostat. To determine issue with duct work, we will need to bring camera system to scope duct system. To fix any duct issue will require removal of a portion of the downstairs ceiling, possible plenum repairs, and unknown duct repairs. Repair of duct system is not economical feasible for affected rooms, and temperature swing can be mitigated by adjusting ducts in downstairs area of home.
Installation of new units and duct work form home.
Upon arrival I notice that the blower capacitor is. 10uf and it was reading 9.1; customer wanted it replaced so I replaced blower capacitor and while running check after capacitor was replaced the contractors started chattering inside the system, I then opened up system and noticed that both contractors are completely burnt/pitted customer elected to replaced contractors and remove blower capacitor, heater is working great..
14â€ wide 20â€ deep found leaking coil New coil installed and cooling well Equipment has been registered with carrier for warranty info
Inspected system for anything that would cause the sour smell, checked blower compartment, checked coil, added a tee and vent into drain and poured bleach down drain and flushed it with water, also poured bleach into drain pan and flushed with water
Inspected furnace for issues and system is running as it should, changed filters, blew out drain and tightened drain to drain pan to prevent water leakage, also insulated flue pipe
System giving code 13 which is limit circuit lockout, the high limit switch was tripped... filters were clogged, changed filters and system was heating well.. the high limit was close to being out of tolerance.. I recommend replacing Replaced both high limit controls
Bad door switch... wired around door switch to keep heat going and will order switch and be back next week to install
Upon arrival system gave code for system lockout, filters are dirty, control board is not sending power to gas valve at all times... itâ€™s hit or miss when it works, it may work multiple times but eventually it stops for awhile and causes system lockout.. control board needs replaced and we will take extra off for no finding issue faster
Upon arrival heater was turned off and pressure switch was make shift jumpered so I plugged pressure switch back up properly and started system and it fired right up, I cycled thru system multiple times to ensure system was working properly and system fired up everytime I checked all 4 limit control and they all work correctly, also checked blower amps and the system is working as it should
Customer called with complaint of heater not working. We previously had been to the helmet two months ago and found no issues when heater was doing the same thing. No service call charge your dispatch charge on this trip due to previous call with no symptoms found. On this call found that the gas valve is not opening in allowing gas to flow to the burner. Gas valve was getting voltage but would not open. Replaced gas valve with OEM part. Checked for gas leak with combustible gas detector and found no presence of gas. Checked with leak detection liquid and found no gas leak present. Heater is working correctly with no other issues found.
No one answered the doorbell or me knocking on the door. Tried calling muiltple times and no one answered, system is running well, capacitor was out of tolerance on heat pump causing compressor amps to run high, changed out capacitor and compressor amps are rising up again but this time more slowly, canâ€™t guarantee the compressor operation but itâ€™s working right now
Heater not working upon arrival. Found blown secondary fuse. Could not find a short. Replaced fuse and heater is working.
Cleaned flame sensor, checked limits (3), checked blower capacitor 15uf= 14.6 , blew out pressure switch hose, checked blower amps running 8.7 max per data plate is 9.5, checked inducer draft motor amps 1.3 max per data label is 1.71, checked temp rise 69 return 112 supply, used customers filters to change the filters, checked home for CO 0ppm, system is heating the best it can right now, customer stated that he changed filters a week ago and filters were dirty today- also stated that system would come on and run for 5-10mins then shut off a week ago before he changed filters, I notified customer that he should call us back when problem is occurring Check to see if customer qualifies for oge cool saver program