Customer stated that after I left on the visit on Friday everything was working properly. Today I verified that all zones are opening and closing properly. She is still wanting her front door installed.
Adjust zone dampers to slow down airflow in upstairs bedroom and top of stair landing. Also to Pushmore to Deniseâ€˜s bedroom. Need to order two newMotors for the zone dampers. One that controls the kitchen and bathroom next to kitchen is not operating.
Arrived to grill condensating I believe we need to increase both the main truck line of the duct and the duct itself seal the boot with mastic and weatherstrip the grill to stop the sweating will contact office with info
AC performance tune up times one system. Upon arrival I cleaned up the front door hardware. It was all over the door handle and deadbolt. The paint on the door looks very unprofessional. Changed out and supplied 20 x 25 x 4 filter. Inspect blower, evaporator and ductwork. Cast thermostat for proper operations. Verified primary drain is clear at this time. Check outdoor unit. Refrigerant level acceptable at this time. Washed condenser coil. Made a note on the maintenance form for the holly bushes to be trimmed back away from the condenser. Barely enough room to wash condenser coil. We need at least 18 " all the way around condenser so that it may be serviced. System is operating at manufacturer specs at this time.
Repaired whistling PVC issue on an AC system in Addison
I spent on replacing Lennox system in Addison
Estimate on replacing air conditioning heating system in Addison