Very efficient and On time Outstanding
Jason was extremely knowledgeable and very helpful with the diagnosis of the system. Highly recommend
Return today to install new universal 1/3 hp 825 RPM condenser fan motor. System operating at manufacture specs at this time.
Completed maintenance check, Drains are clear, condenser coils were dirty, washed coils. Run capacitor/fan motor and compressor amps are in range. Recommended adding start assist to system. Everything else is good working order.
Completed diagnosis, replaced 45/5 Turbo run capacitor for Masterbedroom condenser.
Adjusted dampers in game room, increased airflow in daughters bedroom.
Completed maintenance check out, cleared drains, washed condenser coils,compressor amps on run was good but not on start up. Added hard start assist to both compressors to lower Lra amps. Refrigerant levels and changed out media filters, Temperature splits were great. Everything else is working fine.
AC performance tune up times three systems. Change. 103 filters that Tom supplied. Other two filters look new. Inspect blowers, evaporators and ductwork. Verified all primary drains are clear at this time. Checked Zone systems for proper operations. Test thermostats for proper operation. Check outdoor units. Added 1 lb r410a two main unit. We will monitor system to see if it needs more next year. If so we will give options. Test capacitors and contactors. Replace capacitor on master bedroom unit. Run capacitor comes with a five-year warranty. Washed condenser coils. Systems operating at manufacturer specs at this time.
Return today and found furnace not running. 24 volts was being distributed by the board to the gas valve. Quoting New furnace.
No heat. Upon arrival I went to the Attic and client turned system to heat. Sequence of operations was perfect. System came on and I let it run for 2 or 3 minutes. Went downstairs and pull thermostat off sub base wires going to thermostat or not very tight. Tightened all five system came on and operating properly at this time.
Niose was coming from a crease that had split in the mastic and always vibrating when the blower kicked on because it was sucking in air. Crease was taped up along with flue pipe. System working properly at this time.
This includes new supply plenum, new duct runs with dampers for complete control of airflow, all 4 thermostats wired correctly and at least 1 fresh air vent wired in. Along with adding dampers to the return air allowing you to choke back the daughters which will raise the humidity.
Heat performance tune up times three systems. Cleaned all flame sensors. Tested all safety features. Changed out 20 by 25 by 4 filter Tom supplied. Systems operating at MFG specs at time on all systems but the master. Master is oversized and has an outdated bypass and is going off on a high limit error code. This was shown and explained to the customer along with the solution of a lower fan speed which he declined. High static will result in poor performance, blower issues, and shorter life span. Many of the registers are wring and blow directly onto or into the area of the thermostat. Can confirm heat is running on all systems at this time
Arrived to find systems all with airflow issues and thermostats incorrectly wired. Will send quote to fix daughters room and rewire thermostats correctly to both heat the house and dehumidify. Can confirm ac and heat are running just not efficiently.
Return today to install new inducer motor. Verified no carbon monoxide or gas leaks present. System operating at MFG specs at this time.
No heat downstairs. Inducer motor defective. Ordering Thursday am
Heat precision tuneup x2 systems. Inspect blowers, evaporators and ductwork. Clean flame sensor and induce reports. Hair style safety features. Supplied one of two filters. Systems operating at manufacturer specs at this time.