Jason was very passionate and knowledgeable
We prefer Joel, because we know he will be honest with us. He has been serving our Airconitioner for at least 18 years.
Through check of the system. Informed me of the results and expectations of the system.
Joel S. is an awesome technician. Just bought our house so I wanted everything checked out and tuned up. As usual, AC Pros did a great job. Always happy with their work.
Perform 2 system maintence washed condenser coils changed supplied filters checked refrigerant levels and capacitors both system are cooling properly at this moment
Return today to install another blower motor upstairs. System came on and is operating properly at this time. # no
Completed diagnosis, possible leak in upstairs evaporator coil. Customer will call home warranty for service.
Replace defective blower motor on upstairs unit. Check charge and added1 pound of R 22. System cooling properly at this time.
Completed diagnosis, system was giving me a 126 error code. Repaired corroded wires inside of condenser. Replaced about 4ft of low voltage wire, and reset fault codes. Recommended maintenance agreement, declined at this time.
Performed electronic leak search, found crack in evaporator coil.
left quote for 16 and 18 seer completes 4 ton
AC performance tune up times one system. Inspect blower, evaporator and ductwork. Found inside of furnace cabinet completely covered with sheetrock dust. Recommended to Elizabeth that she is breathing this and it needs to be cleaned. Also cleaned evaporator coil with solution in place. Old blower and pull blower wheel out to clean separately. Check thermostat for proper operations. Check outdoor unit. Refrigerant level good at this time. System is operating at manufacturer specs at this time.
Completed a/c maintenance check out, flushed drains,blower/condenser fan amps were good. Compressor amps, found run capacitor below range. Installed Turbo capacitor 70/5. No other problems found. Also talked to customer about surge protectors, declined at this time
Arrived to find system not starting due to bad capacitor and turbo was Installed. Turbo capacitor and 3 lbs of refrigerant were added and customer will call about maintenance.
Ac checkup on unit. Inside unit checked along with blower and coil. Condenser checked, air speed checked, fllter checked. Condenser was rinsed and freon was balanced. Compressor Amps, contactor and capacitor all.with range at this time. Suggestions are to fix the drain lines which I'll an estimate for in the invoice. Also to add dampers
2 system Maintenance on trane units. Both condensers checked along with compressor Amps, fan amps, capacitors and hard starts. Capacitor on upstairs was low and replaced with turbo cap. Airflow was also adjusted and turned down on both units. Both condensers were rinsed and pressures for units its will be attached to invoice. BothÂ furnaces were checked, filters checked, blowers checked and the only issue found was with the drain lines. I highly recommend fixing the drains since upstairs system is lacking flood prevention to shut off unit if it does back up.Â Drains cover replacement and come with am ez trap. Can confirm ac is running at this time on all units.Â
AC performance tune up times one system. Filter clean at this time. Inspect blower, evaporator and ductwork. Test thermostat for proper operation. Check outdoor unit. Refrigerant level is okay at this time. Test capacitor and contactor. Wash condenser coil. System operating at manufacturer specs at this time.
Heat checkup /ac checkup on heat pump. Pics of pressures will be attached and system components working at this time. Can confirm heat and ac are running at this time.
Ac checkup on 3 trane systems. Pressures for all 3 attached as pics. 2 appear to be low but tends are the 60s and its raining. Recommendations are for hard start kits on all the units and for a drain line upgrade on one of the 3 in the attic. Can confirm ac is running at this time.