I thought he spent too much time on his phone. Made me wonder how much he was concentrating on the job at hand.
Joel was very polite and super quick.
Service in McKinney within an hour on Saturday no extra charge.
Jason was very passionate and knowledgeable
We prefer Joel, because we know he will be honest with us. He has been serving our Airconitioner for at least 18 years.
Through check of the system. Informed me of the results and expectations of the system.
Heating performance tuneup times one system. Change out filter client supplied. Inspect blower, evaporator, ductwork and heat exchangers. Found no stress cracks and heat exchangers. No carbon monoxide or gas leaks detected in home. Test all safety features high limits and rollouts. Check thermostat for proper operations. System operating at manufactures bags at this time.
Completed maintenance inspection, recommend surge protectors for insde units. Flame patterns were good, no gas or carbon monoxide leaks. Changed out media filters. Also homeowner purchased surge protectors.
Completed diagnosis, installed Turbo run capacitor, 25/5. Freon was low, declined repairs at this time.
No cool upstairs. Found float switch tripped because the drain was clogged up. Isolated both units with the quick blast we installed and cleared with nitrogen. The drain line itself was clear. There was some buildup in the P-trap. I treated with drain solution and system is flowing properly at this time.
Outdoor compressor/fan motor was not working. Installed Turbo run capacitor 45/5. Also customer purchased gold membership, 1st visit in fall.
Completed maintenance check, drains lines are clear, filter is clean, refrigerant levels are in range. Everything seems to be working properly.
Arrived to condenser not coming on found bad capacitor replaced with turbo system came on system cooling at this moment
Arrived to primary drain clogged unclogged it with nitrogen and strap drains advised to have a plumber come check out the 90 degree fitting when pvc drains comes out to see if itâ€™s pitching correctly that could be the culprit system draining properly at this moment
No cool. Condenser not running. Found condenser fan motor defective. Removed and replaced with new universal. System cooling properly at this time
Arrived to primary line clogged installed quick blast and nitrogen clear the line system draining properly
Perform 2 system maintence washed condenser coils changed supplied filters checked refrigerant levels and capacitors both system are cooling properly at this moment
Return today to install another blower motor upstairs. System came on and is operating properly at this time. # no
Completed diagnosis, possible leak in upstairs evaporator coil. Customer will call home warranty for service.
Replace defective blower motor on upstairs unit. Check charge and added1 pound of R 22. System cooling properly at this time.
Completed diagnosis, system was giving me a 126 error code. Repaired corroded wires inside of condenser. Replaced about 4ft of low voltage wire, and reset fault codes. Recommended maintenance agreement, declined at this time.