This company is always top notch! Been with them for years with the annual service plan.
I always ask for Joel. He has been helping me for years and does a great job.
No cool single system heat pump. Condenser not running. Found contactor to be defective. Removed and replaced with new double pole contactor. Verified charge is correct at this time. System operating at manufacturers bags at this time.
Clear primary drain line so that float switch wood on trip and air conditioner will come on. Cleared with nitrogen in AC came back on and working properly. The UV light that's installed now is a fluorescent. Cole did not leave the LED version. The fluorescent bulb is working so I told Michael if there was a price difference we would make it up to him somehow.
Need to come back with the pressure switch designed by manufacturer to function properly.
Heating performance tune up times two systems. Kevin changes his own filters. Inspect blower, evaporators and ductwork. Tested all safety features High limits and roll out. Check heat exchanger for cracks found none. No gas leaks or carbon monoxide detected in home. Tighten all wire connections. Evaporator coils clean at this time. Test the thermostat for proper operations. Systems operating at manufacturer specs at this time.
Both Reme halos had a bad board. Installed a non LED until we replace with LED.
Replaced dome sensor. While replacing I found that it was chewed through by a rodent. Charging labor not part per Misty. Also diagnosed a failed LED Reme halo.
Hitting performance tune up times one system. System is a heat pump. Testing amp draw on 10 KW heat strips. 21.03 amps each. Tested safety features of a air handler. Flying change out filter themselves. Program thermostat to acknowledge auxiliary Heat. Check outdoor unit. Refrigerant level good at this time. Tested defrost cycle. Tested capacitor 38.8 microfarads on the compressor side five on the fan side. Wash condenser coil. System operating at manufacturer specs at this time.
System working properly in heat mode. Reme halo is not functioning at this time. Found a bad transformer. Replaced transformer and Reme halo did not come back on. Will fix new hen I return Friday. Thermostat has ERR 067.04 (dome temperature sensor). Drive is sending 3.2VDC to dome sensor. Dome sensor has no resistance. Diagnosed a bad dome sensor.
Heating performance tune up times two systems. Clean flame sensor, induced reports and burners. Tighten all wire connections. Tested all safety features High limits and roll outs. Check heat exchanger for cracks found none. Check for gas leaks found none. No carbon monoxide detected in home. Tested thermostats for proper operations. Systems are operating at manufacturer specs at this time.
Heating checkup on 2 Trane units. All temoertures and pressures are within range but airflow was an issue and on both systems theybwerenset down to the lowest cfm possible. Drain lines were addressed as well and customer was informed on the benefits of changing his thermostat which would allow him fully utilize his new furnave
Follow up on diamonds service call on 8:16. Inspected unit while it was running. It is a 3 ton unit pulling 11.6 amps. Run capacitor with 44 .4 + 5. Cabinet had many loose screws on it. Tighten all screws and replace some with bigger screws. System is more quiet at this time. No charge today since I did not make any kind of repair.
No cool. Follow up from Damon. System was grossly overcharged. Recovered 7# R410 A. Changed out blower motor and module. High pressure switch was stuck open not allowing contactor to engage. Found no leak on evaporator. Office will credit bk monies Damon charged.
Installed LED Reme Halo with air proving switch. Post install walkthrough. All duct installed correctly and hung high and tight. All connections sealed properly. Condenser is set level. Added 2lbs of r410a to get proper subcooling.
Found downstairs system low on R420a charge. With customer approval. Recharged system.
Repairing condensate drain lines in Rowlett