Jeff was precisely on time, worked efficiently, and was able to answer all my questions easily.
This company is always top notch! Been with them for years with the annual service plan.
I always ask for Joel. He has been helping me for years and does a great job.
Install pressure kit for UV light
AC performance tuneup times one system. Inspect blower, evaporator and ductwork. Verified primary drain is clear at this time. Check thermostat for proper operations. Check outdoor Unit. Refrigerant level is good at this time. Check capacitor and contactor her. Capacitor is at 80 ÂµF. Wash condenser coil. System is operating at manufacture specs at this time.
Completed maintenance inspection, washed condenser coils, drains are clear. Refrigerant levels are in range. Everything is. Working fine. Customer has a Remi Halo issues, will call him back next week with resolution.
AC performance tuneup times two systems. Inspect blowers, evaporators and ductwork. Check thermostats for proper operations. Check outdoor units. Refrigerant levels good on both systems. Test capacitors and contactors. Wash condenser coil â€˜s. System is operating at manufacture specs at this time.
No cool upstairs. Found blower motor not working. Changed out the 12.5 ÂµF run capacitorâ€˜s. Motor would not come on. I pulled motor out and brought out to my van and cleaned the inside of the motor. This will not last this is only a temporary fix office to get price for new blower motor
No cool downstairs. Installers had broken low-voltage wire to outdoor unit. Made necessary repairs system came on and operating properly at this time. Extra time due to Robert and I discussing possible duct changes to his home. No charge today
AC performance tuneup x 1 system. Inspect blower, evaporator and ductwork verify primary drain is clear at this time. Check thermostat for proper operations. Filter is 20Ã—25Ã—1. It is going to need to be changed within the next week. Check outdoor unit. Refrigerant level good at this time. Checked capacitors and contactors. Main run capacitor was swollen and defective. Hard start capacitor had a burnt wire. System should not have been running but it was. Replaced capacitor with turbo 200. Run capacitor comes with a five year warranty. Wash condenser coil thoroughly. System cooling properly at this time.
replace blower motor with new - 90 days parts warranty - 30 days labor warranty
No cool on upstairs unit. Diagnosed two days last week with no luck. Downloaded the call cloud for HVAC that Amanda has to offer. Outdoor unit is not getting voltage. Control wire is broke someplace. Will need to run new wire in order for system to operate. I treated drain lines since Robert said the downstairs wasFlowing into the emergency. Office will call and schedule date to do control wire. Given the circumstances of the heat weâ€™re having I am not sure when we can do it. Cost is $750.
Perform 2 system maintenance washed condenser coil checked capacitors ,and split specs are on maintenance form Both systems cooling properly at this moment
AC performance tuneup times two systems. Verified primary drains are clear at this time. Filters are needing to be changed at this time. Both systems are 20Ã—25x4. Check thermostats for proper operations. Inspect blowers, evaporators and ductwork. Check outdoor units. Upstairs unit is in need of repairs. Needs new run capacitor and electrical issues taken care of inside the electrical panel. Jim to give quote for new system upstairs. Washed condenser coilâ€˜s. Checked capacitors and contactors on downstairs unit. Replaced 35 ÂµF run capacitor on downstairs unit. Downstairs is cooling properly at this time.
No cool single system heat pump. Condenser not running. Found contactor to be defective. Removed and replaced with new double pole contactor. Verified charge is correct at this time. System operating at manufacturers bags at this time.
Clear primary drain line so that float switch wood on trip and air conditioner will come on. Cleared with nitrogen in AC came back on and working properly. The UV light that's installed now is a fluorescent. Cole did not leave the LED version. The fluorescent bulb is working so I told Michael if there was a price difference we would make it up to him somehow.
Need to come back with the pressure switch designed by manufacturer to function properly.
Heating performance tune up times two systems. Kevin changes his own filters. Inspect blower, evaporators and ductwork. Tested all safety features High limits and roll out. Check heat exchanger for cracks found none. No gas leaks or carbon monoxide detected in home. Tighten all wire connections. Evaporator coils clean at this time. Test the thermostat for proper operations. Systems operating at manufacturer specs at this time.