His knowledge and expertise is unsurpassed.
On time, respectful
Eric S came to my home today and performed the seasonal maintenance. He was polite and professional
Very friendly service man. I would recommend AC Today for your AC needs
Ac service call. I found the 1 pole contactor and 35/5 capacitor had failed. Replaced both components and the system is cooling properly. We need to Bill voa.
HVAC REPAIR. NEEDS NEW BLOWER MODULE 1/3HP AND A RUN CAP 30/5/370 I talked to Kelli and she said get done as soon as we can.
Quoting three systems for premier as well as cash.
System not keeping up. Thermostat sits in direct sunlight from front door. Customer is going to put curtains up put .5 lb 410 a in to adjust subcool
Completed maintenance. Filter cabinet was missing the filter door. Client will look for it in their garage. Need to call trane for filter pricing and call client with quote for filters and maintenance plan. See photos for filter info.
I told customer we would wave dispatch fee if he replaced or repaired.
Ac is a prtec unit cannot check pressures found dirty blower wheel cleaned blower wheel in place system is now cooling
Air conditioning 2nd opinion quote given for new gas furnace 3 ton whole system(case coil with gas furnace and condenser) also included a 1 yr uv system and duct sanitizer. Customer will call if she wants to go with the install. Date given was Wednesday 5/11 after noon.
No cool found clogged drain cleared drain and flushed drain with drain solve. If drain persists must add trap and vent
Provided and installed 2 portable ac units. Informed client to keep a towel under them and keep an eye on them for any condensation on the towels.
Warranty compressor replacement. The AC system is operating at manufacturers specs.