Very professional and helpful.
Marcus was knowledgeable and friendly. Answered all of my questions clearly and patiently. I asked for some quotes and he provided those for me before he even left the premises.
I had Quinton come out to my place and perform a pre season inspection / tune up on my HVAC system. Very pleased with ALL that he did for us.
Response from AC Today Heating & Air Conditioning:
Thank you William for the kind review. Quinton is one of the best! Our pleasure.
Eric was very personable, polite and respectful. He explained the service he did and answered all of my questions in detail.
Perform maintenance on ac system. Unit in new condition and cooling properly.
I replaced the manufacturers capacitor and checked the pump. Everything seems to be operating properly.
Ac repair: Air handler was not draining properly. Unit was filling up with water and spilling out of pan into the insulation. When the fan shut off the water would then start draining properly. Re ran drain line into condensate pump and the unit will now run for longer periods but is still getting shut down from water in the float switch. It was getting late and home owner was okay with me coming back on Monday since I made it better. Please call the homeowner and schedule for a technician to come out and further diagnose the problem.
Unit in good condition and cooling properly
. The drain line pitch isn’t enough and it’s very slow. The homeowner has bike tires and parts hanging on to and across the drain line. This was more and likely from the homeowner but I flushed and cleared again. It’s clear and draining. The air handler has a lot of condensation on the bottom. See photos. The drain line has6 pvc 90’s. I sent an estimate to install a condensate pump.
Unit in good condition and cooling properly.
Ac maintenance on comfort maker package unit
Air conditioning maintenance performed and customer was very happy to learn about his thermostat functions and filter procedure.
Air conditioning maintenance performed on package unit
Ac service call. The technician found the 70/10 capacitor had failed. The technician only had a 70/5 capacitor. We need to return to install a 70/10. We will have to order it from Trane.
Ac maintenance on 2021 package unit
The technician performed a 1 of 2 friends and family maintenance plan. The tech found a start capacitor lower than manufacturers specs. The compressor is over amping on start up. A start assist is highly recommended to keep the AC running properly. Lastly there is a serious biological growth issue inside the system. The customer is aware of the 3 problems. He stated he just upgraded both bathrooms. He said he will call the company back when he recouped from the bathrooms remodels.