Air conditioning maintenance performed On convenient store location. System is now clean and cooling better than before. Owner of Convienent store is very happy.
Ac maintenance performed. The technician found a capacitor lower than manufacturers specs. Highly recommend replacement before a failure occurs.
Air conditioning service performed, unit had a capacitor at condenser that was at 13 mfd and the contactor was pitted. Found the charge to be 148/610......over charged, I corrected charge to 133/300 replaced both cap and contactor under parts warranty and charged customer 1 hour labor due to revisit after Bryce did maintenance. Customer gets 6 month extension on maintenance agreement as well, per Melissa
Air conditioning service performed found arching disconnect in attic for air handler. Replaced with correct style disconnect box. Collected on site
Completed maintenance on York ac system, all amps and pressures are in range, filter is changed by customer. Flushed and vacuumed drain line, no signs of bio growth found in ac system.
Completed AC tune up on Noradyne package unit. System working great for 8 years old. Changed all filters inside home. Customer moving back to PA permanently.
Performing a maintenance on the Hvac system. All major components on the AC are operating at manufacturers specs. Float switch issue, drain problem as well.