Performed AC maintenance, system operating normally mechanically. Found biological growth in air handler. Sprayed and treated growth with bio side, removed all surface build up and recommended installing UV light. Cleared drain line and treated with drain solve. Flushed with a gallon of water as well. Added new fitting onto drain line outside complementary, drain line was running into the dirt causing drain line to back up. Thank you
Air conditioning maintenance #2 of 2 performed
The customer approved 3lbs of 410A refrigerant. We need to call him in the morning and collect. I sent him a repair option and replacement option. I informed him that if he goes with the replacement we would Ave the cost of the refrigerant
Completed maintenance on a trane package air conditioning system. Tenant will pick up some filters and replace on a regular schedule
Performed a AC maintenance on a 5Year old system. The customer has been using another company for the past few years. The aren’t interested in a maintenance plan or any upgrades
Arrived to perform a comp maintenance on a AC package unit. The units in very bad shape and I couldn’t perform the maintenance. Quoted 2 AC replacement options. 5 TON ST COOL
Performed a AC maintenance. 2 of 2 gold plan. All components are operating properly at this time. Found growth inside the package unit. Also this system isn’t protected by a surge protection.