Client stated on the Honeywell app for his tstat he would at random lose connection to his main tstat but not for the second systems tstat. On arrival tstat was set to 76 and the home was at 76. Checked over ac system for operation. Found a small trace of dye on the service valve cap for the heat pump, tightened schraider on heat pump service valve. Flushed the drain. Checked drain safety switch. System is operating normally and has been since at the house.
Found condenser fan blade causing excessive vibration also found condenser fan motor amperage is slightly higher than what it’s rated for. Talked about repair versus replace and the premiere program. Give a quote to replace the motor and fan blade. Please email maintenance plan renewal quote.
Tune up performed on two split systems
Air conditioning repair on a York air conditioning system.
Found the main unit was low on refrigerant. Checked praise joints where refrigerant piping connects to the condenser and the air handler for a leak and did not find one there. Added refrigerant and UV dye. Need to schedule a return trip to locate the leak.
AC repair on a Lennox air conditioning system. Upon arrival both float switches were removed from the equipment and one humidistat was set to off. Client stated there was water in the float switch reservoir. Flush 2 gallons of water into each systems drain In the water drained out perfectly fine. Put float switch is back in place set humidistat to on where it should be and started both systems to check operation. Both systems are functioning normal at this time.
There is no pan under the coil. Blower motor was causing water to hit plenum. Alex & Ramiro installed a piece of metal to stop the water from going into the plenum. Unit working correctly.
found float switch leaking again. replaced float switch housing and used teflon tape on threads.
Ac refrigerant line repair. Recovered remaining refrigerant repaired leak pressure tested vacuum system down and charged 19 lbs 410a